---
title: N2X(F)K2Y
sku: N2X(F)K2Y-high-voltage-cables
description: >
  The N2X(F)K2Y high-voltage cable series, designed for 64/110kV applications,
  utilizes copper conductors and XLPE insulation to meet the rigorous demands of
  industrial power distribution and transmission. These cables are engineered
  for high ampacity and fault current withstand in diverse installation
  environments.
categories:
  - High Voltage Cables
images: []
application: >
  The N2X(F)K2Y high-voltage cable series is tailored for robust performance in
  high-voltage power systems, featuring copper conductors and cross-linked
  polyethylene (XLPE) insulation. This combination ensures high dielectric strength
  and excellent thermal cycling resistance, crucial for maintaining integrity and
  functionality over long operational periods.
locale: en
---
<ProductTabs technicalData={<ProductTechnicalData data={{
  "technicalItems": [
    {
      "label": "Rated voltage (kV)",
      "value": "64/110",
      "unit": "kV"
    }
  ],
  "voltageTables": [
    {
      "voltageLabel": "64/110 kV",
      "metaItems": [
        {
          "label": "Voltage",
          "value": "64/110 kV"
        }
      ],
      "columns": [
        {
          "key": "Cond",
          "label": "Cond."
        },
        {
          "key": "RI",
          "label": "RI [Ohm/km]"
        },
        {
          "key": "Wi",
          "label": "Wi [mm]"
        },
        {
          "key": "Rbv",
          "label": "Rbv [mm]"
        },
        {
          "key": "Ø",
          "label": "Ø [mm]"
        },
        {
          "key": "G",
          "label": "G [kg/km]"
        }
      ],
      "rows": [
        {
          "configuration": "1×150RM",
          "cells": [
            "Cu",
            "0.16",
            "18",
            "1.4",
            "67",
            "8300"
          ]
        },
        {
          "configuration": "1×185RM",
          "cells": [
            "Cu",
            "0.13",
            "17",
            "1.3",
            "66",
            "8400"
          ]
        },
        {
          "configuration": "1×240RM",
          "cells": [
            "Cu",
            "0.1",
            "16.5",
            "1.4",
            "67",
            "9030"
          ]
        },
        {
          "configuration": "1×300RM",
          "cells": [
            "Cu",
            "0.08",
            "15.5",
            "1.4",
            "67",
            "9540"
          ]
        },
        {
          "configuration": "1×400RM",
          "cells": [
            "Cu",
            "0.06",
            "14.5",
            "1.4",
            "69",
            "10410"
          ]
        },
        {
          "configuration": "1×500RM",
          "cells": [
            "Cu",
            "0.05",
            "14",
            "1.4",
            "71",
            "11590"
          ]
        },
        {
          "configuration": "1×630RM",
          "cells": [
            "Cu",
            "0.04",
            "14",
            "1.5",
            "75",
            "13470"
          ]
        },
        {
          "configuration": "1×800RM",
          "cells": [
            "Cu",
            "0.03",
            "14",
            "1.6",
            "80",
            "15590"
          ]
        },
        {
          "configuration": "1×1000RM",
          "cells": [
            "Cu",
            "0.03",
            "14",
            "1.7",
            "84",
            "17980"
          ]
        },
        {
          "configuration": "1×1200RMS",
          "cells": [
            "Cu",
            "0.02",
            "14",
            "1.8",
            "89",
            "20530"
          ]
        },
        {
          "configuration": "1×1400RMS",
          "cells": [
            "Cu",
            "0.02",
            "14",
            "1.9",
            "94",
            "22780"
          ]
        },
        {
          "configuration": "1×1600RMS",
          "cells": [
            "Cu",
            "0.02",
            "14",
            "2",
            "98",
            "25280"
          ]
        },
        {
          "configuration": "1×1800RMS",
          "cells": [
            "Cu",
            "0.02",
            "14",
            "2",
            "102",
            "27940"
          ]
        },
        {
          "configuration": "1×2000RMS",
          "cells": [
            "Cu",
            "0.02",
            "14",
            "2.1",
            "103",
            "29610"
          ]
        },
        {
          "configuration": "1×2500RMS",
          "cells": [
            "Cu",
            "0.01",
            "14.5",
            "2.2",
            "112",
            "35400"
          ]
        },
        {
          "configuration": "1×3000RMS",
          "cells": [
            "Cu",
            "0.01",
            "14.5",
            "2.4",
            "121",
            "42420"
          ]
        }
      ]
    }
  ]
}} />}>

<section>
<h2>Engineering Overview</h2>
<p>The <strong>N2X(F)K2Y high-voltage cable series</strong> is tailored for robust performance in high-voltage power systems, featuring copper conductors and cross-linked polyethylene (XLPE) insulation. This combination ensures high dielectric strength and excellent thermal cycling resistance, crucial for maintaining integrity and functionality over long operational periods.</p>
</section>
<section>
<h2>Technical Performance and Installation</h2>
<p>Designed to support a wide range of industrial applications, the N2X(F)K2Y cable series excels in environments requiring high ampacity and effective fault current management. The cables' construction supports efficient heat dissipation and reduces the risk of thermal degradation even under high load conditions.</p>
<ul>
<li>Optimal <strong>ampacity</strong> to support increased power transmission requirements.</li>
<li>Enhanced <strong>fault current withstand</strong> capability to ensure reliability and safety.</li>
<li>Superior <strong>dielectric strength</strong>, facilitated by high-quality XLPE insulation.</li>
</ul>
<p>Installation techniques such as <strong>trefoil formation</strong>, <strong>direct burial</strong>, and <strong>cable tray mounting</strong> are compatible with this series, providing flexibility and ease of deployment in varied operational landscapes.</p>
</section>
<section>
<h2>Compliance and Electromagnetic Compatibility</h2>
<p>The N2X(F)K2Y series adheres to stringent <strong>IEC standards</strong> and meets <strong>CPR classification</strong> requirements, ensuring compliance with international safety and quality benchmarks. Additionally, the cables are designed to minimize electromagnetic interference, enhancing <strong>electromagnetic compatibility (EMC)</strong> and reducing induced voltages, which is critical in densely packed power installations.</p>
<ul>
<li>Robust <strong>metallic screening</strong> to mitigate EMC issues and manage fault currents effectively.</li>
<li>CE marking confirms that the cable series meets the essential requirements of relevant European directives.</li>
</ul>
</section>

</ProductTabs>
