../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-vendor-DOMPurify-DOMPurify.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-assets-js-external-permalinks.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-js-front-end-breeze-prefetch-links.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-jquery-jquery.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-jquery-jquery-migrate.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-min-svgs-inline-vanilla-min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-zoom-jquery.zoom.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-photoswipe-photoswipe.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-photoswipe-photoswipe-ui-default.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-frontend-single-product.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-jquery-blockui-jquery.blockUI.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-js-cookie-js.cookie.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-frontend-woocommerce.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-dist-scripts-url-shortify.js
Skip to main content
Hit enter to search or ESC to close
Close Search

# NA2XSY

The NA2XSY cable is a medium-voltage cable with aluminium conductor, XLPE insulation, and copper shielding, suitable for underground installation. It is designed for demanding power distribution tasks and stands out for its high operational reliability, excellent installation properties, and thermal resistance up to 90 °C.

Request Cable
Email *
Request *
If you are human, leave this field blank.
SKU: NA2XSY-medium-voltage-cables Category: Medium Voltage Cables

- Description

## Description

### For high-performance medium-voltage networks

The NA2XSY meets the requirements of DIN VDE 0276-620, HD 620 S2, and IEC 60502. It is suitable for installation indoors, in cable ducts, underground, in water, or outdoors – but only when installed with protection. Typical areas of application include industrial plants, power stations, and switching stations where medium voltage must be transported with high operational safety.

### Technical construction

The conductor consists of multi-stranded aluminium (Class 2 according to VDE 0295 / IEC 60228). The XLPE insulation is permanently bonded to the outer conductive layer to ensure a partial discharge-free structure. The structure also includes an inner conductive layer, conductive tape, a copper wire screen with counter helix, additional tape, and a red PVC sheath. The cable is flame-retardant and approved for underground installation (depending on the type).

### Application and properties

Thanks to its precise construction, the NA2XSY can also be easily installed in complex routing scenarios. It is free from silicone and cadmium, contains no paint-wetting impairment substances, and withstands short-circuit temperatures up to +250 °C. The concentric structure and tightly bonded conductive layers make this cable a reliable solution for medium-voltage power distribution where operational safety and ease of installation are essential.

## Datasheet

Configuration | Rated Voltage | Test Voltage | Maximal Short Circuit Temperature | Maximal Operating Conductor Temperature | Minimal Temperature For Laying | Operating Temperature Range | Colour Of Sheath | Packaging | RoHS/REACH | Bending Radius
--- | --- | --- | --- | --- | --- | --- | --- | --- | --- | ---
1x120/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 450 mm
1x35/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 360 mm
1x50/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 375 mm
1x70/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 405 mm
1x95/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 420 mm
1x150/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 465 mm
1x185/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 495 mm
1x185/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 495 mm
1x240/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 525 mm
1x300/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 570 mm
1x400/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 600 mm
1x500/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 645 mm
1x630/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 705 mm
1x800/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 765 mm
1x1000/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 855 mm
1x50/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 435 mm
1x70/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 465 mm
1x95/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 480 mm
1x120/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 510 mm
1x150/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 540 mm
1x185/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 555 mm
1x185/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 555 mm
1x240/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 585 mm
1x300/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 615 mm
1x400/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 660 mm
1x500/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 720 mm
1x630/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 765 mm
1x800/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 840 mm
1x1000/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 915 mm
1x50/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 510 mm
1x70/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 540 mm
1x95/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 555 mm
1x120/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 585 mm
1x150/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 600 mm
1x185/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 630 mm
1x240/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 660 mm
1x300/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 690 mm
1x400/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 735 mm
1x500/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 795 mm
1x630/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 840 mm
1x800/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 915 mm
1x1000/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 1005 mm

### Other Specifications

Configuration

Conductor

Insulation

Conductive Tape Below Screen

Copper Wire Screen And Tape

Non Conducting Tape Above Screen

Al Foil

Sheath

Number Of Cores And Cross Section

Minimal Storage Temperature

Colour Of Insulation

Flame Retardant

CPR Class

CE Conformity

Shape Of Conductor

Conductor Diameter

Nominal Insulation Thickness

Diameter Over Insulation

Minimum Sheath Thickness

Outer Diameter

Weight

DC Resistance At 20 °C

Capacitance

Inductance, Trefoil

Inductance In Air, Flat 1

Inductance In Ground, Flat 1

Conductor Shortcircuit Current

Screen Shortcircuit Current

Heating Time Constant, Trefoil

Heating Time Constant, Flat

Current Ratings In Air, Trefoil

Current Ratings In Air, Flat

Current Ratings In Ground, Trefoil

Current Ratings In Ground, Flat

1x120/16 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x120/16 | -25 °C | uncoloured | EN 60 332-1-6 | Eca | yes | RM | 12.8 mm | 3.4 mm | 20.9 mm | 2.1 mm | 30 mm | 1036 kg/km | 0.253 Ω/km | 0.34 μF/km | 0.36 | 0.53 | 0.62 | 11.3 kA | 3.2 kA | 541 | 393 | 321 | 384 | 283 | 318
1x35/16 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x35/16 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 7.2 mm | 3.4 mm | 15.3 mm | 2.1 mm | 24 mm | 668 kg/km | 0.868 Ω/km | 0.22 μF/km | 0.44 | 0.61 | 0.74 | 3.3 kA | 3.2 kA | 197 | 140 | 153 | 182 | 145 | 165
1x50/16 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x50/16 | -25 °C | uncoloured | EN 60 332-1-3 | Eca | yes | RM | 8.3 mm | 3.4 mm | 16.4 mm | 2.1 mm | 25 mm | 734 kg/km | 0.641 Ω/km | 0.25 μF/km | 0.42 | 0.6 | 0.71 | 4.7 kA | 3.2 kA | 278 | 198 | 183 | 219 | 171 | 194
1x70/16 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x70/16 | -25 °C | uncoloured | EN 60 332-1-4 | Eca | yes | RM | 9.8 mm | 3.4 mm | 17.9 mm | 2.1 mm | 27 mm | 824 kg/km | 0.443 Ω/km | 0.28 μF/km | 0.39 | 0.57 | 0.68 | 6.6 kA | 3.2 kA | 363 | 260 | 228 | 273 | 208 | 236
1x95/16 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x95/16 | -25 °C | uncoloured | EN 60 332-1-5 | Eca | yes | RM | 11.3 mm | 3.4 mm | 19.4 mm | 2.1 mm | 28 mm | 932 kg/km | 0.32 Ω/km | 0.31 μF/km | 0.37 | 0.54 | 0.65 | 9 kA | 3.2 kA | 452 | 325 | 278 | 333 | 248 | 281
1x150/25 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x150/25 | -25 °C | uncoloured | EN 60 332-1-7 | Eca | yes | RM | 14.2 mm | 3.4 mm | 22.3 mm | 2.1 mm | 31 mm | 1222 kg/km | 0.206 Ω/km | 0.37 μF/km | 0.34 | 0.51 | 0.59 | 14.2 kA | 5 kA | 667 | 501 | 364 | 432 | 315 | 350
1x185/16 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x185/16 | -25 °C | uncoloured | EN 60 332-1-8 | Eca | yes | RM | 15.8 mm | 3.4 mm | 23.9 mm | 2.1 mm | 33 mm | 1283 kg/km | 0.164 Ω/km | 0.4 μF/km | 0.34 | 0.51 | 0.59 | 17.5 kA | 3.2 kA | 762 | 563 | 418 | 496 | 357 | 394
1x185/25 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x185/25 | -25 °C | uncoloured | EN 60 332-1-9 | Eca | yes | RM | 15.8 mm | 3.4 mm | 23.9 mm | 2.1 mm | 33 mm | 1372 kg/km | 0.164 Ω/km | 0.41 μF/km | 0.33 | 0.49 | 0.57 | 17.5 kA | 5 kA | 771 | 590 | 418 | 496 | 357 | 394
1x240/25 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x240/25 | -25 °C | uncoloured | EN 60 332-1-10 | Eca | yes | RM | 18.1 mm | 3.4 mm | 26.2 mm | 2.1 mm | 35 mm | 1579 kg/km | 0.125 Ω/km | 0.44 μF/km | 0.32 | 0.48 | 0.55 | 22.7 kA | 5 kA | 955 | 745 | 494 | 583 | 413 | 452
1x300/25 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x300/25 | -25 °C | uncoloured | EN 60 332-1-11 | Eca | yes | RM | 20.2 mm | 3.4 mm | 28.3 mm | 2.1 mm | 38 mm | 1834 kg/km | 0.1 Ω/km | 0.48 μF/km | 0.31 | 0.47 | 0.54 | 28.4 kA | 5 kA | 1146 | 907 | 568 | 666 | 466 | 506
1x400/35 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x400/35 | -25 °C | uncoloured | EN 60 332-1-12 | Eca | yes | RM | 23.3 mm | 3.4 mm | 31.4 mm | 2.1 mm | 40 mm | 2263 kg/km | 0.0778 Ω/km | 0.54 μF/km | 0.29 | 0.45 | 0.5 | 37.8 kA | 7 kA | 1549 | 1315 | 660 | 755 | 529 | 558
1x500/35 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x500/35 | -25 °C | uncoloured | EN 60 332-1-13 | Eca | yes | RM | 26.5 mm | 3.4 mm | 34.6 mm | 2.1 mm | 43 mm | 2643 kg/km | 0.0605 Ω/km | 0.62 μF/km | 0.28 | 0.43 | 0.48 | 47.3 kA | 7 kA | 1823 | 1575 | 767 | 868 | 602 | 627
1x630/35 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x630/35 | -25 °C | uncoloured | EN 60 332-1-14 | Eca | yes | RM | 29.9 mm | 3.4 mm | 38 mm | 2.1 mm | 47 mm | 3120 kg/km | 0.0469 Ω/km | 0.67 μF/km | 0.27 | 0.42 | 0.46 | 59.6 kA | 7 kA | 2237 | 2000 | 840 | 889 | 681 | 661
1x800/35 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x800/35 | -25 °C | uncoloured | EN 60 332-1-15 | Eca | yes | RM | 34.2 mm | 3.4 mm | 42.3 mm | 2.4 mm | 51 mm | 3760 kg/km | 0.0367 Ω/km | 0.76 μF/km | 0.26 | 0.41 | 0.44 | 75.6 kA | 7 kA | 2800 | 2546 | 953 | 1000 | 754 | 725
1x1000/35 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x1000/35 | -25 °C | uncoloured | EN 60 332-1-16 | Eca | yes | RM | 38.1 mm | 3.4 mm | 46.2 mm | 2.4 mm | 57 mm | 4724 kg/km | 0.0291 Ω/km | 0.84 μF/km | 0.25 | 0.4 | 0.42 | 94 kA | 7 kA | 3505 | 3157 | 1187 | 1270 | 852 | 842
1x50/16 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x50/16 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 8.3 mm | 5.5 mm | 20.5 mm | 2.1 mm | 29 mm | 936 kg/km | 0.641 Ω/km | 0.17 μF/km | 0.44 | 0.62 | 0.72 | 4.7 kA | 3.2 kA | 276 | 204 | 185 | 219 | 172 | 195
1x70/16 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x70/16 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 9.8 mm | 5.5 mm | 22 mm | 2.1 mm | 31 mm | 1037 kg/km | 0.443 Ω/km | 0.19 μF/km | 0.42 | 0.6 | 0.69 | 6.6 kA | 3.2 kA | 351 | 261 | 231 | 273 | 210 | 237
1x95/16 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x95/16 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 11.3 mm | 5.5 mm | 23.5 mm | 2.1 mm | 32 mm | 1157 kg/km | 0.32 Ω/km | 0.21 μF/km | 0.4 | 0.58 | 0.66 | 9 kA | 3.2 kA | 442 | 328 | 280 | 332 | 251 | 282
1x120/16 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x120/16 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 12.8 mm | 5.5 mm | 25 mm | 2.1 mm | 34 mm | 1274 kg/km | 0.253 Ω/km | 0.23 μF/km | 0.39 | 0.56 | 0.64 | 11.3 kA | 3.2 kA | 532 | 397 | 323 | 384 | 285 | 319
1x150/25 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x150/25 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 14.2 mm | 5.5 mm | 26.4 mm | 2.1 mm | 36 mm | 1491 kg/km | 0.206 Ω/km | 0.25 μF/km | 0.37 | 0.54 | 0.61 | 14.2 kA | 5 kA | 653 | 500 | 366 | 432 | 319 | 352
1x185/16 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x185/16 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 15.8 mm | 5.5 mm | 28 mm | 2.1 mm | 37 mm | 1546 kg/km | 0.164 Ω/km | 0.27 μF/km | 0.36 | 0.53 | 0.6 | 17.5 kA | 3.2 kA | 753 | 570 | 420 | 494 | 361 | 396
1x185/25 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x185/25 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 15.8 mm | 5.5 mm | 28 mm | 2.1 mm | 37 mm | 1636 kg/km | 0.164 Ω/km | 0.27 μF/km | 0.36 | 0.52 | 0.59 | 17.5 kA | 5 kA | 760 | 590 | 420 | 494 | 361 | 396
1x240/25 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x240/25 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 18.1 mm | 5.5 mm | 30.3 mm | 2.1 mm | 39 mm | 1863 kg/km | 0.125 Ω/km | 0.3 μF/km | 0.35 | 0.51 | 0.57 | 22.7 kA | 5 kA | 920 | 729 | 496 | 581 | 417 | 455
1x300/25 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x300/25 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 20.2 mm | 5.5 mm | 32.4 mm | 2.1 mm | 41 mm | 2084 kg/km | 0.1 Ω/km | 0.32 μF/km | 0.33 | 0.49 | 0.55 | 28.4 kA | 5 kA | 1110 | 895 | 569 | 663 | 471 | 510
1x400/35 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x400/35 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 23.3 mm | 5.5 mm | 35.5 mm | 2.1 mm | 44 mm | 2567 kg/km | 0.0778 Ω/km | 0.36 μF/km | 0.32 | 0.47 | 0.51 | 37.8 kA | 7 kA | 1474 | 1262 | 660 | 753 | 535 | 564
1x500/35 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x500/35 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 26.5 mm | 5.5 mm | 38.7 mm | 2.1 mm | 48 mm | 2992 kg/km | 0.0605 Ω/km | 0.4 μF/km | 0.3 | 0.46 | 0.49 | 47.3 kA | 7 kA | 1724 | 1525 | 766 | 866 | 609 | 634
1x630/35 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x630/35 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 29.9 mm | 5.5 mm | 42.1 mm | 2.4 mm | 51 mm | 3520 kg/km | 0.0469 Ω/km | 0.44 μF/km | 0.29 | 0.44 | 0.48 | 59.6 kA | 7 kA | 2105 | 1895 | 866 | 913 | 697 | 664
1x800/35 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x800/35 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 34.2 mm | 5.5 mm | 46.4 mm | 2.4 mm | 56 mm | 4182 kg/km | 0.0367 Ω/km | 0.49 μF/km | 0.28 | 0.43 | 0.46 | 75.6 kA | 7 kA | 2546 | 2376 | 1000 | 1035 | 780 | 734
1x1000/35 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x1000/35 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 38.1 mm | 5.5 mm | 50.3 mm | 2.4 mm | 61 mm | 5165 kg/km | 0.0291 Ω/km | 0.54 μF/km | 0.27 | 0.42 | 0.44 | 94.6 kA | 7 kA | 3116 | 2917 | 1130 | 1168 | 868 | 809
1x50/16 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x50/16 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 8.3 mm | 8 mm | 25.5 mm | 2.1 mm | 34 mm | 1176 kg/km | 0.641 Ω/km | 0.13 μF/km | 0.48 | 0.65 | 0.73 | 4.7 kA | 3.2 kA | 269 | 206 | 187 | 219 | 174 | 195
1x70/16 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x70/16 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 9.8 mm | 8 mm | 27 mm | 2.1 mm | 36 mm | 1290 kg/km | 0.443 Ω/km | 0.15 μF/km | 0.45 | 0.63 | 0.7 | 6.6 kA | 3.2 kA | 344 | 264 | 232 | 273 | 213 | 238
1x95/16 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x95/16 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 11.3 mm | 8 mm | 28.5 mm | 2.1 mm | 37 mm | 1421 kg/km | 0.32 Ω/km | 0.16 μF/km | 0.43 | 0.61 | 0.67 | 9 kA | 3.2 kA | 433 | 334 | 282 | 331 | 254 | 283
1x120/16 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x120/16 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 12.8 mm | 8 mm | 30 mm | 2.1 mm | 39 mm | 1548 kg/km | 0.253 Ω/km | 0.17 μF/km | 0.41 | 0.58 | 0.65 | 11.3 kA | 3.2 kA | 530 | 408 | 325 | 382 | 289 | 321
1x150/25 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x150/25 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 14.2 mm | 8 mm | 31.4 mm | 2.1 mm | 40 mm | 1757 kg/km | 0.206 Ω/km | 0.19 μF/km | 0.4 | 0.57 | 0.62 | 14.2 kA | 5 kA | 640 | 509 | 367 | 429 | 322 | 354
1x185/25 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x185/25 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 15.8 mm | 8 mm | 33 mm | 2.1 mm | 42 mm | 1930 kg/km | 0.164 Ω/km | 0.2 μF/km | 0.39 | 0.55 | 0.6 | 17.5 kA | 5 kA | 744 | 599 | 421 | 492 | 364 | 399
1x240/25 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x240/25 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 18.1 mm | 8 mm | 35.3 mm | 2.1 mm | 44 mm | 2172 kg/km | 0.125 Ω/km | 0.22 μF/km | 0.37 | 0.53 | 0.58 | 22.7 kA | 5 kA | 905 | 737 | 496 | 578 | 422 | 458
1x300/25 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x300/25 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 20.2 mm | 8 mm | 37.4 mm | 2.1 mm | 46 mm | 2424 kg/km | 0.1 Ω/km | 0.24 μF/km | 0.35 | 0.52 | 0.56 | 28.4 kA | 5 kA | 1092 | 907 | 568 | 659 | 476 | 514
1x400/35 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x400/35 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 23.3 mm | 8 mm | 40.5 mm | 2.1 mm | 49 mm | 2928 kg/km | 0.0778 Ω/km | 0.27 μF/km | 0.34 | 0.49 | 0.53 | 37.8 kA | 7 kA | 1453 | 1284 | 659 | 750 | 541 | 570
1x500/35 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x500/35 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 26.5 mm | 8 mm | 43.7 mm | 2.4 mm | 53 mm | 3390 kg/km | 0.0605 Ω/km | 0.29 μF/km | 0.33 | 0.48 | 0.5 | 47.3 kA | 7 kA | 1724 | 1541 | 764 | 861 | 616 | 642
1x630/35 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x630/35 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 29.9 mm | 8 mm | 47.1 mm | 2.4 mm | 56 mm | 3937 kg/km | 0.0469 Ω/km | 0.32 μF/km | 0.31 | 0.46 | 0.49 | 59.6 kA | 7 kA | 2052 | 1921 | 877 | 907 | 702 | 672
1x800/35 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x800/35 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 34.2 mm | 8 mm | 51.4 mm | 2.9 mm | 61 mm | 4667 kg/km | 0.0367 Ω/km | 0.36 μF/km | 0.3 | 0.45 | 0.47 | 75.6 kA | 7 kA | 2546 | 2461 | 1000 | 1017 | 780 | 742
1x1000/35 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PVC | 1x1000/35 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 38.1 mm | 8 mm | 55.3 mm | 3 mm | 67 mm | 5703 kg/km | 0.0291 Ω/km | 0.39 μF/km | 0.29 | 0.44 | 0.45 | 94.6 kA | 7 kA | 3050 | 3050 | 1142 | 1142 | 877 | 824

## Related products

- ## NA2XS2Y

- ## N2XS2Y

- ## N2XS(FL)2Y

- ## N2XSY

Share Share Share Pin
Close Menu

#### KLZ Cables

Raiffeisenstraße 22
73630 Remshalden

[email protected]

../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-salient-social-js-salient-social.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-build-third-party-jquery.easing.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-build-third-party-jquery.mousewheel.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-build-priority.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-build-third-party-transit.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-build-third-party-waypoints.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-build-third-party-imagesLoaded.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-build-third-party-hoverintent.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-build-third-party-jquery.fancybox.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-build-third-party-anime.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-build-third-party-superfish.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-build-init.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-build-nectar-smooth-scroll.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-build-third-party-flickity.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-build-nectar-single-product.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-third-party-touchswipe.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-js-front-end-breeze-lazy-load.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-sourcebuster-sourcebuster.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-frontend-order-attribution.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-build-nectar-delay-javascript.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-formidable-pro-js-frm.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-dist-hooks.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsy-1-44573-js-build-gtag-events.js