../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-vendor-DOMPurify-DOMPurify.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-assets-js-external-permalinks.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-js-front-end-breeze-prefetch-links.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-jquery-jquery.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-jquery-jquery-migrate.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-min-svgs-inline-vanilla-min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-zoom-jquery.zoom.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-photoswipe-photoswipe.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-photoswipe-photoswipe-ui-default.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-frontend-single-product.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-jquery-blockui-jquery.blockUI.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-js-cookie-js.cookie.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-frontend-woocommerce.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-dist-scripts-url-shortify.js
Skip to main content
Hit enter to search or ESC to close
Close Search

# N2XS(FL)2Y

The N2XS(FL)2Y cable is a longitudinally watertight medium-voltage cable with a copper conductor, XLPE insulation, and a tightly bonded Al/PE sheath. It offers maximum operational safety for critical infrastructures and provides reliable protection against penetrating moisture.

Request Cable
Email *
Request *
If you are human, leave this field blank.
SKU: N2XS(FL)2Y-medium-voltage-cables Category: Medium Voltage Cables

- Description

## Description

### For demanding power distribution networks

The N2XS(FL)2Y meets the standards DIN VDE 0276-620, HD 620 S2 and IEC 60502. It is ideally suited for installation indoors, in cable ducts, outdoors, in soil, in water, and on cable trays – especially in utility grids, industrial plants, and switching stations, where high demands on mechanical strength and water resistance apply.

### Technical construction

The cable design is based on a multi-stranded copper conductor (Class 2), an XLPE insulation with an extruded, tightly bonded outer conductive layer, and a longitudinally watertight, conductive tape. The shielding consists of copper wires with counter helix, complemented by an additional longitudinally watertight tape. The outer protection is achieved with a black PE sheath laminated with an aluminum tape – serving as an effective water barrier.

### Properties and benefits

The N2XS(FL)2Y is suitable for underground installation, designed for outdoor use, and withstands operating temperatures up to +90 °C and short-circuit loads up to +250 °C. It is free from silicone and cadmium and contains no substances that interfere with paint wetting. Thanks to its partial discharge-free design and the Al/PE layer, it is ideally suited for humid environments with high safety requirements.

## Datasheet

Configuration | Rated Voltage | Test Voltage | Maximal Short Circuit Temperature | Maximal Operating Conductor Temperature | Minimal Temperature For Laying | Operating Temperature Range | Colour Of Sheath | Packaging | RoHS/REACH | Bending Radius
--- | --- | --- | --- | --- | --- | --- | --- | --- | --- | ---
1x50/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 520 mm
1x70/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 560 mm
1x95/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 580 mm
1x120/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 620 mm
1x150/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 640 mm
1x185/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 680 mm
1x240/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 720 mm
1x300/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 780 mm
1x400/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 840 mm
1x500/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 880 mm
1x50/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - + 90 °C | black | wooden or metal drums | N/A | 600 mm
1x70/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 640 mm
1x95/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - + 90 °C | black | wooden or metal drums | N/A | 660 mm
1x120/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - + 90 °C | black | wooden or metal drums | N/A | 700 mm
1x150/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - + 90 °C | black | wooden or metal drums | N/A | 720 mm
1x185/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - + 90 °C | black | wooden or metal drums | N/A | 760 mm
1x240/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - + 90 °C | black | wooden or metal drums | N/A | 800 mm
1x300/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - + 90 °C | black | wooden or metal drums | N/A | 860 mm
1x400/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - + 90 °C | black | wooden or metal drums | N/A | 900 mm
1x500/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - + 90 °C | black | wooden or metal drums | N/A | 980 mm
1x50/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 700 mm
1x70/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 740 mm
1x95/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 760 mm
1x120/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 800 mm
1x150/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 820 mm
1x185/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 860 mm
1x240/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 900 mm
1x300/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 960 mm
1x400/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 1020 mm
1x500/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 1080 mm

### Other Specifications

Configuration

Conductor

Insulation

Conductive Tape Below Screen

Copper Wire Screen And Tape

Non Conducting Tape Above Screen

Al Foil

Sheath

Number Of Cores And Cross Section

Minimal Storage Temperature

Colour Of Insulation

Flame Retardant

CPR Class

CE Conformity

Shape Of Conductor

Conductor Diameter

Nominal Insulation Thickness

Diameter Over Insulation

Minimum Sheath Thickness

Outer Diameter

Weight

DC Resistance At 20 °C

Capacitance

Inductance, Trefoil

Inductance In Ground, Flat 1

Conductor Shortcircuit Current

Screen Shortcircuit Current

Heating Time Constant, Trefoil

Heating Time Constant, Flat

Current Ratings In Air, Trefoil

Current Ratings In Air, Flat

Current Ratings In Ground, Trefoil

Current Ratings In Ground, Flat

1x50/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x50/16 | –35 °C | uncoloured | no | Fca | yes | RM | 8.2 mm | 3.4 mm | 16.3 mm | 2.1 mm | 26 mm | 1010 kg/km | 0.387 Ω/km | 0.24 μF/km | 0.41 | 0.7 | 7.1 kA | 3.2 kA | 383 | 273 | 238 | 282 | 220 | 249
1x70/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x70/16 | –35 °C | uncoloured | no | Fca | yes | RM | 9.8 mm | 3.4 mm | 17.9 mm | 2.1 mm | 28 mm | 1238 kg/km | 0.268 Ω/km | 0.28 μF/km | 0.39 | 0.67 | 10 kA | 3.2 kA | 490 | 353 | 294 | 350 | 268 | 302
1x95/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x95/16 | –35 °C | uncoloured | no | Fca | yes | RM | 11.3 mm | 3.4 mm | 19.4 mm | 2.1 mm | 29 mm | 1495 kg/km | 0.193 Ω/km | 0.3 μF/km | 0.37 | 0.65 | 13.6 kA | 3.2 kA | 618 | 450 | 358 | 426 | 320 | 359
1x120/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x120/16 | –35 °C | uncoloured | no | Fca | yes | RM | 12.8 mm | 3.4 mm | 20.9 mm | 2.1 mm | 31 mm | 1773 kg/km | 0.153 Ω/km | 0.34 μF/km | 0.36 | 0.62 | 17.1 kA | 3.2 kA | 742 | 545 | 413 | 491 | 363 | 405
1x150/25 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x150/25 | –35 °C | uncoloured | no | Fca | yes | RM | 14.2 mm | 3.4 mm | 22.3 mm | 2.1 mm | 32 mm | 2119 kg/km | 0.124 Ω/km | 0.36 μF/km | 0.34 | 0.59 | 21.4 kA | 5 kA | 927 | 719 | 468 | 549 | 405 | 442
1x185/25 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x185/25 | –35 °C | uncoloured | no | Fca | yes | RM | 15.8 mm | 3.4 mm | 23.9 mm | 2.1 mm | 34 mm | 2483 kg/km | 0.099 Ω/km | 0.4 μF/km | 0.33 | 0.58 | 26.4 kA | 5 kA | 1094 | 866 | 535 | 625 | 456 | 493
1x240/25 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x240/25 | –35 °C | uncoloured | no | Fca | yes | RM | 18.3 mm | 3.4 mm | 26.4 mm | 2.1 mm | 36 mm | 3073 kg/km | 0.075 Ω/km | 0.44 μF/km | 0.32 | 0.55 | 34.3 kA | 5 kA | 1335 | 1091 | 631 | 731 | 526 | 563
1x300/25 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x300/25 | –35 °C | uncoloured | no | Fca | yes | RM | 20.7 mm | 3.4 mm | 28.8 mm | 2.1 mm | 39 mm | 3737 kg/km | 0.06 Ω/km | 0.48 μF/km | 0.31 | 0.54 | 42.9 kA | 5 kA | 1595 | 1336 | 722 | 831 | 591 | 626
1x400/35 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x400/35 | –35 °C | uncoloured | no | Fca | yes | RM | 23.3 mm | 3.4 mm | 31.4 mm | 2.1 mm | 42 mm | 4697 kg/km | 0.047 Ω/km | 0.54 μF/km | 0.29 | 0.5 | 57.2 kA | 7 kA | 2303 | 2036 | 827 | 920 | 662 | 675
1x500/35 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x500/35 | –35 °C | uncoloured | no | Fca | yes | RM | 26.5 mm | 3.4 mm | 34.6 mm | 2.1 mm | 44 mm | 5729 kg/km | 0.037 Ω/km | 0.61 μF/km | 0.28 | 0.48 | 71.4 kA | 7 kA | 2803 | 2538 | 949 | 1043 | 744 | 748
1x50/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x50/16 | -35 °C | uncoloured | no | Fca | yes | RM | 8.2 mm | 5.5 mm | 20.5 mm | 2.1 mm | 30 mm | 1166 kg/km | 0.387 Ω/km | 0.17 μF/km | 0.45 | 0.72 | 7.1 kA | 3.2 kA | 369 | 276 | 239 | 282 | 222 | 250
1x70/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x70/16 | -35 °C | uncoloured | no | Fca | yes | RM | 9.8 mm | 5.5 mm | 22.1 mm | 2.1 mm | 32 mm | 1409 kg/km | 0.268 Ω/km | 0.19 μF/km | 0.42 | 0.68 | 10 kA | 3.2 kA | 471 | 355 | 297 | 351 | 271 | 303
1x95/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x95/16 | -35 °C | uncoloured | no | Fca | yes | RM | 11.3 mm | 5.5 mm | 23.6 mm | 2.1 mm | 33 mm | 1675 kg/km | 0.193 Ω/km | 0.21 μF/km | 0.41 | 0.66 | 13.6 kA | 3.2 kA | 591 | 451 | 361 | 426 | 323 | 360
1x120/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x120/16 | -35 °C | uncoloured | no | Fca | yes | RM | 12.8 mm | 5.5 mm | 25.1 mm | 2.1 mm | 35 mm | 1968 kg/km | 0.153 Ω/km | 0.23 μF/km | 0.39 | 0.64 | 17.1 kA | 3.2 kA | 718 | 554 | 416 | 491 | 367 | 407
1x150/25 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x150/25 | -35 °C | uncoloured | no | Fca | yes | RM | 14.2 mm | 5.5 mm | 26.5 mm | 2.1 mm | 36 mm | 2320 kg/km | 0.124 Ω/km | 0.25 μF/km | 0.37 | 0.6 | 21.4 kA | 5 kA | 897 | 723 | 470 | 549 | 409 | 445
1x185/25 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x185/25 | -35 °C | uncoloured | no | Fca | yes | RM | 15.8 mm | 5.5 mm | 28.1 mm | 2.1 mm | 38 mm | 2697 kg/km | 0.099 Ω/km | 0.27 μF/km | 0.36 | 0.59 | 26.4 kA | 5 kA | 1063 | 871 | 538 | 625 | 461 | 498
1x240/25 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x240/25 | -35 °C | uncoloured | no | Fca | yes | RM | 18.3 mm | 5.5 mm | 30.6 mm | 2.1 mm | 40 mm | 3303 kg/km | 0.075 Ω/km | 0.3 μF/km | 0.35 | 0.56 | 34.3 kA | 5 kA | 1300 | 1091 | 634 | 731 | 532 | 568
1x300/25 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x300/25 | -35 °C | uncoloured | no | Fca | yes | RM | 20.7 mm | 5.5 mm | 33 mm | 2.1 mm | 43 mm | 3978 kg/km | 0.06 Ω/km | 0.32 μF/km | 0.34 | 0.55 | 42.9 kA | 5 kA | 1568 | 1350 | 724 | 830 | 599 | 633
1x400/35 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x400/35 | -35 °C | uncoloured | no | Fca | yes | RM | 23.3 mm | 5.5 mm | 35.6 mm | 2.1 mm | 45 mm | 4925 kg/km | 0.047 Ω/km | 0.36 μF/km | 0.32 | 0.51 | 57.2 kA | 7 kA | 2230 | 2085 | 829 | 923 | 671 | 685
1x500/35 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x500/35 | -35 °C | uncoloured | no | Fca | yes | RM | 26.5 mm | 5.5 mm | 38.8 mm | 2.1 mm | 49 mm | 6006 kg/km | 0.037 Ω/km | 0.4 μF/km | 0.3 | 0.49 | 71.4 kA | 7 kA | 2727 | 2614 | 953 | 1045 | 754 | 760
1x50/16 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x50/16 | -35 °C | uncoloured | no | Fca | yes | RM | 8.2 mm | 8 mm | 25.5 mm | 2.1 mm | 35 mm | 1405 kg/km | 0.387 Ω/km | 0.13 μF/km | 0.48 | 0.73 | 7.1 kA | 3.2 kA | 360 | 280 | 241 | 282 | 225 | 251
1x70/16 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x70/16 | -35 °C | uncoloured | no | Fca | yes | RM | 9.8 mm | 8 mm | 27.1 mm | 2.1 mm | 37 mm | 1646 kg/km | 0.268 Ω/km | 0.15 μF/km | 0.45 | 0.7 | 10 kA | 3.2 kA | 462 | 362 | 299 | 350 | 274 | 304
1x95/16 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x95/16 | -35 °C | uncoloured | no | Fca | yes | RM | 11.3 mm | 8 mm | 28.6 mm | 2.1 mm | 38 mm | 1926 kg/km | 0.193 Ω/km | 0.16 μF/km | 0.43 | 0.67 | 13.6 kA | 3.2 kA | 583 | 459 | 363 | 425 | 327 | 362
1x120/16 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x120/16 | -35 °C | uncoloured | no | Fca | yes | RM | 12.8 mm | 8 mm | 30.1 mm | 2.1 mm | 40 mm | 2227 kg/km | 0.153 Ω/km | 0.17 μF/km | 0.42 | 0.65 | 17.1 kA | 3.2 kA | 707 | 563 | 418 | 468 | 371 | 409
1x150/25 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x150/25 | -35 °C | uncoloured | no | Fca | yes | RM | 14.2 mm | 8 mm | 31.5 mm | 2.1 mm | 41 mm | 2590 kg/km | 0.124 Ω/km | 0.19 μF/km | 0.4 | 0.62 | 21.4 kA | 5 kA | 876 | 730 | 472 | 548 | 414 | 449
1x185/25 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x185/25 | -35 °C | uncoloured | no | Fca | yes | RM | 15.8 mm | 8 mm | 33.1 mm | 2.1 mm | 43 mm | 2975 kg/km | 0.099 Ω/km | 0.2 μF/km | 0.39 | 0.6 | 26.4 kA | 5 kA | 1032 | 876 | 539 | 624 | 466 | 502
1x240/25 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x240/25 | -35 °C | uncoloured | no | Fca | yes | RM | 18.3 mm | 8 mm | 35.6 mm | 2.1 mm | 45 mm | 3594 kg/km | 0.075 Ω/km | 0.22 μF/km | 0.37 | 0.58 | 34.3 kA | 5 kA | 1274 | 1108 | 635 | 728 | 539 | 574
1x300/25 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x300/25 | -35 °C | uncoloured | no | Fca | yes | RM | 20.7 mm | 8 mm | 38 mm | 2.1 mm | 48 mm | 4300 kg/km | 0.06 Ω/km | 0.24 μF/km | 0.36 | 0.56 | 42.9 kA | 5 kA | 1541 | 1377 | 725 | 828 | 606 | 640
1x400/35 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x400/35 | -35 °C | uncoloured | no | Fca | yes | RM | 23.3 mm | 8 mm | 40.6 mm | 2.1 mm | 51 mm | 5290 kg/km | 0.047 Ω/km | 0.26 μF/km | 0.34 | 0.52 | 57.2 kA | 7 kA | 2206 | 2109 | 831 | 922 | 680 | 695
1x500/35 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x500/35 | -35 °C | uncoloured | no | Fca | yes | RM | 26.5 mm | 8 mm | 43.8 mm | 2.4 mm | 54 mm | 6403 kg/km | 0.037 Ω/km | 0.29 μF/km | 0.32 | 0.5 | 71.4 kA | 7 kA | 2689 | 2652 | 953 | 1045 | 765 | 773

## Related products

- ## NA2XS2Y

- ## N2XS2Y

- ## N2XSY

- ## NA2XS(FL)2Y

Share Share Share Pin
Close Menu

#### KLZ Cables

Raiffeisenstraße 22
73630 Remshalden

[email protected]

../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-salient-social-js-salient-social.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-build-third-party-jquery.easing.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-build-third-party-jquery.mousewheel.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-build-priority.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-build-third-party-transit.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-build-third-party-waypoints.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-build-third-party-imagesLoaded.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-build-third-party-hoverintent.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-build-third-party-jquery.fancybox.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-build-third-party-anime.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-build-third-party-superfish.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-build-init.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-build-nectar-smooth-scroll.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-build-third-party-flickity.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-build-nectar-single-product.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-third-party-touchswipe.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-js-front-end-breeze-lazy-load.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-sourcebuster-sourcebuster.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-frontend-order-attribution.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-build-nectar-delay-javascript.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-formidable-pro-js-frm.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-dist-hooks.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsfl-1-44451-js-build-gtag-events.js