../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-vendor-DOMPurify-DOMPurify.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-assets-js-external-permalinks.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-js-front-end-breeze-prefetch-links.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-jquery-jquery.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-jquery-jquery-migrate.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-min-svgs-inline-vanilla-min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-zoom-jquery.zoom.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-photoswipe-photoswipe.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-photoswipe-photoswipe-ui-default.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-frontend-single-product.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-jquery-blockui-jquery.blockUI.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-js-cookie-js.cookie.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-frontend-woocommerce.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-dist-scripts-url-shortify.js
Skip to main content
Hit enter to search or ESC to close
Close Search

# NA2XS(F)2Y

The NA2XS(F)2Y cable is a longitudinally watertight medium-voltage cable with an aluminium conductor, XLPE insulation, and a durable PE sheath. It is designed for energy-efficient and safe installation in the ground and critical network areas.

Request Cable
Email *
Request *
If you are human, leave this field blank.
SKU: NA2XS(F)2Y-medium-voltage-cables Category: Medium Voltage Cables

- Description

## Description

### For high-performance power networks with enhanced protection requirements

The NA2XS(F)2Y complies with standards DIN VDE 0276-620, HD 620 S2 and IEC 60502. It is suitable for installation indoors, in cable ducts, underground, in water, outdoors, or on cable trays. Its main applications are in utility grids, industrial facilities, and substations, where additional safety reserves against moisture ingress and mechanical stress are required.

### Construction and material characteristics

The conductor consists of multi-stranded aluminium (Class 2), surrounded by an inner conductive layer and XLPE insulation with a tightly bonded outer conductive layer – extruded in a single process for maximum operational safety. The shielding is provided by a copper wire braid with counter helix, complemented by a longitudinally watertight tape. The outer sheath is made of black PE (Type DMP2) and reliably protects against mechanical stress and moisture.

### Properties and fields of application

The NA2XS(F)2Y is suitable for underground installation, free from silicone and cadmium, and resistant to paint-wetting impairment substances. It withstands continuous temperatures up to +90 °C and tolerates short-circuit loads up to +250 °C. Thanks to its well-designed, partial discharge-free structure, it is particularly well suited for safe power distribution in moist and complex installation environments.

## Datasheet

Configuration | Rated Voltage | Test Voltage | Maximal Short Circuit Temperature | Maximal Operating Conductor Temperature | Minimal Temperature For Laying | Operating Temperature Range | Colour Of Sheath | Packaging | RoHS/REACH | Bending Radius
--- | --- | --- | --- | --- | --- | --- | --- | --- | --- | ---
1x50/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 520 mm
1x70/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 560 mm
1x95/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 580 mm
1x120/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 620 mm
1x150/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 640 mm
1x185/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 680 mm
1x240/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 720 mm
1x300/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 780 mm
1x400/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 840 mm
1x500/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 880 mm
1x50/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - + 90 °C | black | wooden or metal drums | N/A | 600 mm
1x70/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 640 mm
1x95/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - + 90 °C | black | wooden or metal drums | N/A | 660 mm
1x120/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - + 90 °C | black | wooden or metal drums | N/A | 700 mm
1x150/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - + 90 °C | black | wooden or metal drums | N/A | 720 mm
1x185/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - + 90 °C | black | wooden or metal drums | N/A | 760 mm
1x240/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - + 90 °C | black | wooden or metal drums | N/A | 800 mm
1x300/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - + 90 °C | black | wooden or metal drums | N/A | 860 mm
1x400/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - + 90 °C | black | wooden or metal drums | N/A | 900 mm
1x500/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - + 90 °C | black | wooden or metal drums | N/A | 980 mm
1x50/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 700 mm
1x70/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 740 mm
1x95/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 760 mm
1x120/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 800 mm
1x150/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 820 mm
1x185/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 860 mm
1x240/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 900 mm
1x300/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 960 mm
1x400/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 1020 mm
1x500/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 1080 mm

### Other Specifications

Configuration

Conductor

Insulation

Conductive Tape Below Screen

Copper Wire Screen And Tape

Non Conducting Tape Above Screen

Al Foil

Sheath

Number Of Cores And Cross Section

Minimal Storage Temperature

Colour Of Insulation

Flame Retardant

CPR Class

CE Conformity

Shape Of Conductor

Conductor Diameter

Nominal Insulation Thickness

Diameter Over Insulation

Minimum Sheath Thickness

Outer Diameter

Weight

DC Resistance At 20 °C

Capacitance

Inductance, Trefoil

Inductance In Ground, Flat 1

Conductor Shortcircuit Current

Screen Shortcircuit Current

Heating Time Constant, Trefoil

Heating Time Constant, Flat

Current Ratings In Air, Trefoil

Current Ratings In Air, Flat

Current Ratings In Ground, Trefoil

Current Ratings In Ground, Flat

1x50/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x50/16 | –35 °C | uncoloured | no | Fca | yes | RM | 8.2 mm | 3.4 mm | 16.3 mm | 2.1 mm | 26 mm | 1010 kg/km | 0.387 Ω/km | 0.24 μF/km | 0.41 | 0.7 | 7.1 kA | 3.2 kA | 383 | 273 | 238 | 282 | 220 | 249
1x70/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x70/16 | –35 °C | uncoloured | no | Fca | yes | RM | 9.8 mm | 3.4 mm | 17.9 mm | 2.1 mm | 28 mm | 1238 kg/km | 0.268 Ω/km | 0.28 μF/km | 0.39 | 0.67 | 10 kA | 3.2 kA | 490 | 353 | 294 | 350 | 268 | 302
1x95/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x95/16 | –35 °C | uncoloured | no | Fca | yes | RM | 11.3 mm | 3.4 mm | 19.4 mm | 2.1 mm | 29 mm | 1495 kg/km | 0.193 Ω/km | 0.3 μF/km | 0.37 | 0.65 | 13.6 kA | 3.2 kA | 618 | 450 | 358 | 426 | 320 | 359
1x120/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x120/16 | –35 °C | uncoloured | no | Fca | yes | RM | 12.8 mm | 3.4 mm | 20.9 mm | 2.1 mm | 31 mm | 1773 kg/km | 0.153 Ω/km | 0.34 μF/km | 0.36 | 0.62 | 17.1 kA | 3.2 kA | 742 | 545 | 413 | 491 | 363 | 405
1x150/25 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x150/25 | –35 °C | uncoloured | no | Fca | yes | RM | 14.2 mm | 3.4 mm | 22.3 mm | 2.1 mm | 32 mm | 2119 kg/km | 0.124 Ω/km | 0.36 μF/km | 0.34 | 0.59 | 21.4 kA | 5 kA | 927 | 719 | 468 | 549 | 405 | 442
1x185/25 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x185/25 | –35 °C | uncoloured | no | Fca | yes | RM | 15.8 mm | 3.4 mm | 23.9 mm | 2.1 mm | 34 mm | 2483 kg/km | 0.099 Ω/km | 0.4 μF/km | 0.33 | 0.58 | 26.4 kA | 5 kA | 1094 | 866 | 535 | 625 | 456 | 493
1x240/25 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x240/25 | –35 °C | uncoloured | no | Fca | yes | RM | 18.3 mm | 3.4 mm | 26.4 mm | 2.1 mm | 36 mm | 3073 kg/km | 0.075 Ω/km | 0.44 μF/km | 0.32 | 0.55 | 34.3 kA | 5 kA | 1335 | 1091 | 631 | 731 | 526 | 563
1x300/25 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x300/25 | –35 °C | uncoloured | no | Fca | yes | RM | 20.7 mm | 3.4 mm | 28.8 mm | 2.1 mm | 39 mm | 3737 kg/km | 0.06 Ω/km | 0.48 μF/km | 0.31 | 0.54 | 42.9 kA | 5 kA | 1595 | 1336 | 722 | 831 | 591 | 626
1x400/35 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x400/35 | –35 °C | uncoloured | no | Fca | yes | RM | 23.3 mm | 3.4 mm | 31.4 mm | 2.1 mm | 42 mm | 4697 kg/km | 0.047 Ω/km | 0.54 μF/km | 0.29 | 0.5 | 57.2 kA | 7 kA | 2303 | 2036 | 827 | 920 | 662 | 675
1x500/35 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x500/35 | –35 °C | uncoloured | no | Fca | yes | RM | 26.5 mm | 3.4 mm | 34.6 mm | 2.1 mm | 44 mm | 5729 kg/km | 0.037 Ω/km | 0.61 μF/km | 0.28 | 0.48 | 71.4 kA | 7 kA | 2803 | 2538 | 949 | 1043 | 744 | 748
1x50/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x50/16 | -35 °C | uncoloured | no | Fca | yes | RM | 8.2 mm | 5.5 mm | 20.5 mm | 2.1 mm | 30 mm | 1166 kg/km | 0.387 Ω/km | 0.17 μF/km | 0.45 | 0.72 | 7.1 kA | 3.2 kA | 369 | 276 | 239 | 282 | 222 | 250
1x70/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x70/16 | -35 °C | uncoloured | no | Fca | yes | RM | 9.8 mm | 5.5 mm | 22.1 mm | 2.1 mm | 32 mm | 1409 kg/km | 0.268 Ω/km | 0.19 μF/km | 0.42 | 0.68 | 10 kA | 3.2 kA | 471 | 355 | 297 | 351 | 271 | 303
1x95/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x95/16 | -35 °C | uncoloured | no | Fca | yes | RM | 11.3 mm | 5.5 mm | 23.6 mm | 2.1 mm | 33 mm | 1675 kg/km | 0.193 Ω/km | 0.21 μF/km | 0.41 | 0.66 | 13.6 kA | 3.2 kA | 591 | 451 | 361 | 426 | 323 | 360
1x120/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x120/16 | -35 °C | uncoloured | no | Fca | yes | RM | 12.8 mm | 5.5 mm | 25.1 mm | 2.1 mm | 35 mm | 1968 kg/km | 0.153 Ω/km | 0.23 μF/km | 0.39 | 0.64 | 17.1 kA | 3.2 kA | 718 | 554 | 416 | 491 | 367 | 407
1x150/25 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x150/25 | -35 °C | uncoloured | no | Fca | yes | RM | 14.2 mm | 5.5 mm | 26.5 mm | 2.1 mm | 36 mm | 2320 kg/km | 0.124 Ω/km | 0.25 μF/km | 0.37 | 0.6 | 21.4 kA | 5 kA | 897 | 723 | 470 | 549 | 409 | 445
1x185/25 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x185/25 | -35 °C | uncoloured | no | Fca | yes | RM | 15.8 mm | 5.5 mm | 28.1 mm | 2.1 mm | 38 mm | 2697 kg/km | 0.099 Ω/km | 0.27 μF/km | 0.36 | 0.59 | 26.4 kA | 5 kA | 1063 | 871 | 538 | 625 | 461 | 498
1x240/25 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x240/25 | -35 °C | uncoloured | no | Fca | yes | RM | 18.3 mm | 5.5 mm | 30.6 mm | 2.1 mm | 40 mm | 3303 kg/km | 0.075 Ω/km | 0.3 μF/km | 0.35 | 0.56 | 34.3 kA | 5 kA | 1300 | 1091 | 634 | 731 | 532 | 568
1x300/25 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x300/25 | -35 °C | uncoloured | no | Fca | yes | RM | 20.7 mm | 5.5 mm | 33 mm | 2.1 mm | 43 mm | 3978 kg/km | 0.06 Ω/km | 0.32 μF/km | 0.34 | 0.55 | 42.9 kA | 5 kA | 1568 | 1350 | 724 | 830 | 599 | 633
1x400/35 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x400/35 | -35 °C | uncoloured | no | Fca | yes | RM | 23.3 mm | 5.5 mm | 35.6 mm | 2.1 mm | 45 mm | 4925 kg/km | 0.047 Ω/km | 0.36 μF/km | 0.32 | 0.51 | 57.2 kA | 7 kA | 2230 | 2085 | 829 | 923 | 671 | 685
1x500/35 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x500/35 | -35 °C | uncoloured | no | Fca | yes | RM | 26.5 mm | 5.5 mm | 38.8 mm | 2.1 mm | 49 mm | 6006 kg/km | 0.037 Ω/km | 0.4 μF/km | 0.3 | 0.49 | 71.4 kA | 7 kA | 2727 | 2614 | 953 | 1045 | 754 | 760
1x50/16 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x50/16 | -35 °C | uncoloured | no | Fca | yes | RM | 8.2 mm | 8 mm | 25.5 mm | 2.1 mm | 35 mm | 1405 kg/km | 0.387 Ω/km | 0.13 μF/km | 0.48 | 0.73 | 7.1 kA | 3.2 kA | 360 | 280 | 241 | 282 | 225 | 251
1x70/16 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x70/16 | -35 °C | uncoloured | no | Fca | yes | RM | 9.8 mm | 8 mm | 27.1 mm | 2.1 mm | 37 mm | 1646 kg/km | 0.268 Ω/km | 0.15 μF/km | 0.45 | 0.7 | 10 kA | 3.2 kA | 462 | 362 | 299 | 350 | 274 | 304
1x95/16 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x95/16 | -35 °C | uncoloured | no | Fca | yes | RM | 11.3 mm | 8 mm | 28.6 mm | 2.1 mm | 38 mm | 1926 kg/km | 0.193 Ω/km | 0.16 μF/km | 0.43 | 0.67 | 13.6 kA | 3.2 kA | 583 | 459 | 363 | 425 | 327 | 362
1x120/16 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x120/16 | -35 °C | uncoloured | no | Fca | yes | RM | 12.8 mm | 8 mm | 30.1 mm | 2.1 mm | 40 mm | 2227 kg/km | 0.153 Ω/km | 0.17 μF/km | 0.42 | 0.65 | 17.1 kA | 3.2 kA | 707 | 563 | 418 | 468 | 371 | 409
1x150/25 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x150/25 | -35 °C | uncoloured | no | Fca | yes | RM | 14.2 mm | 8 mm | 31.5 mm | 2.1 mm | 41 mm | 2590 kg/km | 0.124 Ω/km | 0.19 μF/km | 0.4 | 0.62 | 21.4 kA | 5 kA | 876 | 730 | 472 | 548 | 414 | 449
1x185/25 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x185/25 | -35 °C | uncoloured | no | Fca | yes | RM | 15.8 mm | 8 mm | 33.1 mm | 2.1 mm | 43 mm | 2975 kg/km | 0.099 Ω/km | 0.2 μF/km | 0.39 | 0.6 | 26.4 kA | 5 kA | 1032 | 876 | 539 | 624 | 466 | 502
1x240/25 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x240/25 | -35 °C | uncoloured | no | Fca | yes | RM | 18.3 mm | 8 mm | 35.6 mm | 2.1 mm | 45 mm | 3594 kg/km | 0.075 Ω/km | 0.22 μF/km | 0.37 | 0.58 | 34.3 kA | 5 kA | 1274 | 1108 | 635 | 728 | 539 | 574
1x300/25 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x300/25 | -35 °C | uncoloured | no | Fca | yes | RM | 20.7 mm | 8 mm | 38 mm | 2.1 mm | 48 mm | 4300 kg/km | 0.06 Ω/km | 0.24 μF/km | 0.36 | 0.56 | 42.9 kA | 5 kA | 1541 | 1377 | 725 | 828 | 606 | 640
1x400/35 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x400/35 | -35 °C | uncoloured | no | Fca | yes | RM | 23.3 mm | 8 mm | 40.6 mm | 2.1 mm | 51 mm | 5290 kg/km | 0.047 Ω/km | 0.26 μF/km | 0.34 | 0.52 | 57.2 kA | 7 kA | 2206 | 2109 | 831 | 922 | 680 | 695
1x500/35 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | Yes | PE | 1x500/35 | -35 °C | uncoloured | no | Fca | yes | RM | 26.5 mm | 8 mm | 43.8 mm | 2.4 mm | 54 mm | 6403 kg/km | 0.037 Ω/km | 0.29 μF/km | 0.32 | 0.5 | 71.4 kA | 7 kA | 2689 | 2652 | 953 | 1045 | 765 | 773

## Related products

- ## N2XS2Y

- ## N2XSY

- ## NA2XS(FL)2Y

- ## N2XS(F)2Y

Share Share Share Pin
Close Menu

#### KLZ Cables

Raiffeisenstraße 22
73630 Remshalden

[email protected]

../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-salient-social-js-salient-social.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-build-third-party-jquery.easing.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-build-third-party-jquery.mousewheel.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-build-priority.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-build-third-party-transit.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-build-third-party-waypoints.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-build-third-party-imagesLoaded.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-build-third-party-hoverintent.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-build-third-party-jquery.fancybox.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-build-third-party-anime.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-build-third-party-superfish.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-build-init.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-build-nectar-smooth-scroll.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-build-third-party-flickity.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-build-nectar-single-product.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-third-party-touchswipe.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-js-front-end-breeze-lazy-load.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-sourcebuster-sourcebuster.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-frontend-order-attribution.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-build-nectar-delay-javascript.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-formidable-pro-js-frm.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-dist-hooks.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-44906-js-build-gtag-events.js