../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-vendor-DOMPurify-DOMPurify.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-assets-js-external-permalinks.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-js-front-end-breeze-prefetch-links.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-jquery-jquery.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-jquery-jquery-migrate.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-min-svgs-inline-vanilla-min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-zoom-jquery.zoom.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-photoswipe-photoswipe.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-photoswipe-photoswipe-ui-default.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-frontend-single-product.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-jquery-blockui-jquery.blockUI.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-js-cookie-js.cookie.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-frontend-woocommerce.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-dist-scripts-url-shortify.js
Skip to main content
Hit enter to search or ESC to close
Close Search

# NYCWY

NYCWY cables are robust low-voltage cables with a concentric conductor, suitable for power distribution in buildings, industrial facilities, and underground installations. Thanks to their PVC insulation and sheath, they are mechanically durable, moisture-resistant, and versatile in use – even in concrete or water.

Request Cable
Email *
Request *
If you are human, leave this field blank.
SKU: NYCWY-low-voltage-cables Category: Low Voltage Cables

- Description

## Description

### Versatile use in power distribution

The NYCWY is one of the classic low-voltage cables according to VDE standard and is designed for rated voltages up to 1 kV. It is used wherever reliable energy distribution is required – in buildings, industrial plants, transformer stations, or directly underground. It can also be easily installed in cable trays, concrete environments, or underwater. The choice of materials ensures that this cable withstands even harsh conditions – without the need for additional protective measures.

### Construction and materials

The design is technically well thought out: a copper conductor forms the core, surrounded by PVC insulation that is both mechanically robust and electrically safe. This is followed by a concentric conductor in a corrugated shape, which serves as a protective or return conductor depending on the application. The outer layer is a durable PVC sheath that protects the cable against moisture, pressure, and chemical influences.

### Variants and cross-sections

The NYCWY is available in a wide range of versions – for example, 4×25/16, 4×70/35, or 4×185/95. The first number group indicates the number and cross-section of the current-carrying conductors, the second refers to the concentric conductor. This flexibility allows the cable to be adapted to different network requirements – from house connections to industrial power distribution.

## Datasheet

Configuration | Rated Voltage | Test Voltage | Maximal Short Circuit Temperature | Maximal Operating Conductor Temperature | Minimal Temperature For Laying | Operating Temperature Range | Colour Of Sheath | Packaging | RoHS/REACH | Bending Radius
--- | --- | --- | --- | --- | --- | --- | --- | --- | --- | ---
2x10/10 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
2x16/16 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
3x10/10 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
3x16/16 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
3x25/16 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
3x25/25 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
3x35/16 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
3x35/35 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
3x50/25 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
3x50/50 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
3x70/35 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
3x70/70 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
3x95/50 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
3x95/95 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
3x120/70 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
3x120/120 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
3x150/70 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
3x150/150 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
3x185/95 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
3x185/185 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
3x240/120 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
4x10/10 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
4x16/16 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
4x25/16 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
4x25/25 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
4x35/16 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
4x35/35 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
4x50/25 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
4x50/50 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
4x70/35 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
4x70/70 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
4x95/50 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
4x95/70 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
4x95/95 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
4x120/70 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
4x120/120 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
4x150/70 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
4x185/95 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
4x185/185 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)
4x240/120 - 0.6/1 kV | 0.6/1 kV | 4 kV | 160 °C | 70 °C | -5 °C | -35 - +70 °C | black | cable drums | yes/yes | 15xD (Single core); 12xD (Multi core)

### Other Specifications

Configuration | Conductor | Insulation | CUScreen | Sheath | Number Of Cores And Cross Section | Minimal Storage Temperature | Colour Of Insulation | Self Extinguishing Of Single Cable | CPR Class | Shape Of Conductor | Nominal Insulation Thickness | Nominal Sheath Thickness | Outer Diameter | Weight | Maximum Resistance Of Conductor
--- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | ---
2x10/10 - 0.6/1 kV | CU | PVC | Yes | PVC | 2x10/10 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | RE | 1 mm | 1.8 | 19 mm | 670 kg/km | 1.83
2x16/16 - 0.6/1 kV | CU | PVC | Yes | PVC | 2x16/16 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | RE | 1 mm | 1.8 | 21 mm | 890 kg/km | 1.15
3x10/10 - 0.6/1 kV | CU | PVC | Yes | PVC | 3x10/10 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | RE | 1 mm | 1.8 | 20 mm | 773 kg/km | 1.83
3x16/16 - 0.6/1 kV | CU | PVC | Yes | PVC | 3x16/16 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | RE | 1 mm | 1.8 | 22 mm | 1045 kg/km | 1.15
3x25/16 - 0.6/1 kV | CU | PVC | Yes | PVC | 3x25/16 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | RMV | 1.2 mm | 1.8 | 26 mm | 1490 kg/km | 0.727
3x25/25 - 0.6/1 kV | CU | PVC | Yes | PVC | 3x25/25 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | RMV | 1.2 mm | 1.8 | 26 mm | 1582 kg/km | 0.727
3x35/16 - 0.6/1 kV | CU | PVC | Yes | PVC | 3x35/16 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.2 mm | 1.8 | 26 mm | 1729 kg/km | 0.524
3x35/35 - 0.6/1 kV | CU | PVC | Yes | PVC | 3x35/35 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.2 mm | 1.8 | 26 mm | 1913 kg/km | 0.524
3x50/25 - 0.6/1 kV | CU | PVC | Yes | PVC | 3x50/25 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.4 mm | 1.9 | 29 mm | 2272 kg/km | 0.387
3x50/50 - 0.6/1 kV | CU | PVC | Yes | PVC | 3x50/50 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.4 mm | 1.9 | 30 mm | 2498 kg/km | 0.387
3x70/35 - 0.6/1 kV | CU | PVC | Yes | PVC | 3x70/35 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.4 mm | 2 | 33 mm | 3128 kg/km | 0.268
3x70/70 - 0.6/1 kV | CU | PVC | Yes | PVC | 3x70/70 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.4 mm | 2 | 34 mm | 3473 kg/km | 0.268
3x95/50 - 0.6/1 kV | CU | PVC | Yes | PVC | 3x95/50 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.6 mm | 2.2 | 38 mm | 4177 kg/km | 0.193
3x95/95 - 0.6/1 kV | CU | PVC | Yes | PVC | 3x95/95 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.6 mm | 2.2 | 38 mm | 4640 kg/km | 0.193
3x120/70 - 0.6/1 kV | CU | PVC | Yes | PVC | 3x120/70 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.6 mm | 2.3 | 41 mm | 5168 kg/km | 0.153
3x120/120 - 0.6/1 kV | CU | PVC | Yes | PVC | 3x120/120 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.6 mm | 2.3 | 41 mm | 5674 kg/km | 0.153
3x150/70 - 0.6/1 kV | CU | PVC | Yes | PVC | 3x150/70 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.8 mm | 2.4 | 46 mm | 6193 kg/km | 0.124
3x150/150 - 0.6/1 kV | CU | PVC | Yes | PVC | 3x150/150 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.8 mm | 2.4 | 47 mm | 6982 kg/km | 0.124
3x185/95 - 0.6/1 kV | CU | PVC | Yes | PVC | 3x185/95 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 2 mm | 2.6 | 50 mm | 7689 kg/km | 0.0991
3x185/185 - 0.6/1 kV | CU | PVC | Yes | PVC | 3x185/185 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 2 mm | 2.6 | 51 mm | 8609 kg/km | 0.0991
3x240/120 - 0.6/1 kV | CU | PVC | Yes | PVC | 3x240/120 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 2.2 mm | 2.8 | 56 mm | 9950 kg/km | 0.0754
4x10/10 - 0.6/1 kV | CU | PVC | Yes | PVC | 4x10/10 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | RE | 1 mm | 1.8 | 21 mm | 903 kg/km | 1.83
4x16/16 - 0.6/1 kV | CU | PVC | Yes | PVC | 4x16/16 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | RE | 1 mm | 1.8 | 24 mm | 1237 kg/km | 1.15
4x25/16 - 0.6/1 kV | CU | PVC | Yes | PVC | 4x25/16 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | RMV | 1.2 mm | 1.8 | 28 mm | 1801 kg/km | 0.727
4x25/25 - 0.6/1 kV | CU | PVC | Yes | PVC | 4x25/25 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | RMV | 1.2 mm | 1.8 | 28 mm | 1886 kg/km | 0.727
4x35/16 - 0.6/1 kV | CU | PVC | Yes | PVC | 4x35/16 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.2 mm | 1.8 | 28 mm | 2156 kg/km | 0.524
4x35/35 - 0.6/1 kV | CU | PVC | Yes | PVC | 4x35/35 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.2 mm | 1.8 | 28 mm | 2333 kg/km | 0.524
4x50/25 - 0.6/1 kV | CU | PVC | Yes | PVC | 4x50/25 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.4 mm | 2 | 33 mm | 2944 kg/km | 0.387
4x50/50 - 0.6/1 kV | CU | PVC | Yes | PVC | 4x50/50 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.4 mm | 2 | 34 mm | 3171 kg/km | 0.387
4x70/35 - 0.6/1 kV | CU | PVC | Yes | PVC | 4x70/35 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.4 mm | 2.1 | 36 mm | 3932 kg/km | 0.268
4x70/70 - 0.6/1 kV | CU | PVC | Yes | PVC | 4x70/70 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.4 mm | 2.1 | 37 mm | 4277 kg/km | 0.268
4x95/50 - 0.6/1 kV | CU | PVC | Yes | PVC | 4x95/50 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.6 mm | 2.3 | 42 mm | 5276 kg/km | 0.193
4x95/70 - 0.6/1 kV | CU | PVC | Yes | PVC | 4x95/70 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.6 mm | 2.3 | 42 mm | 5488 kg/km | 0.193
4x95/95 - 0.6/1 kV | CU | PVC | Yes | PVC | 4x95/95 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.6 mm | 2.3 | 42 mm | 5740 kg/km | 0.193
4x120/70 - 0.6/1 kV | CU | PVC | Yes | PVC | 4x120/70 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.6 mm | 2.4 | 46 mm | 6571 kg/km | 0.153
4x120/120 - 0.6/1 kV | CU | PVC | Yes | PVC | 4x120/120 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.6 mm | 2.4 | 46 mm | 7077 kg/km | 0.153
4x150/70 - 0.6/1 kV | CU | PVC | Yes | PVC | 4x150/70 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 1.8 mm | 2.6 | 51 mm | 7883 kg/km | 0.124
4x185/95 - 0.6/1 kV | CU | PVC | Yes | PVC | 4x185/95 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 2 mm | 2.8 | 56 mm | 9892 kg/km | 0.0991
4x185/185 - 0.6/1 kV | CU | PVC | Yes | PVC | 4x185/185 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 2 mm | 2.8 | 57 mm | 10813 kg/km | 0.0991
4x240/120 - 0.6/1 kV | CU | PVC | Yes | PVC | 4x240/120 | -35 °C | HD 308 S2 | IEC 60332-1-2 | Eca | SM | 2.2 mm | 3 | 62 mm | 12658 kg/km | 0.0754

## Related products

- ## NA2XY

- ## NAY2Y

- ## NY2Y

- ## NAYY

Share Share Share Pin
Close Menu

#### KLZ Cables

Raiffeisenstraße 22
73630 Remshalden

[email protected]

../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-salient-social-js-salient-social.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-build-third-party-jquery.easing.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-build-third-party-jquery.mousewheel.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-build-priority.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-build-third-party-transit.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-build-third-party-waypoints.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-build-third-party-imagesLoaded.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-build-third-party-hoverintent.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-build-third-party-jquery.fancybox.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-build-third-party-anime.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-build-third-party-superfish.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-build-init.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-build-nectar-smooth-scroll.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-build-third-party-flickity.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-build-nectar-single-product.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-third-party-touchswipe.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-js-front-end-breeze-lazy-load.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-sourcebuster-sourcebuster.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-frontend-order-attribution.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-build-nectar-delay-javascript.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-formidable-pro-js-frm.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-dist-hooks.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-low-voltage-cables-nycwy-1-42433-js-build-gtag-events.js