---
title: N2X(F)KLD2Y
sku: N2X(F)KLD2Y-high-voltage-cables-2
description: >
  The N2X(F)KLD2Y-high-voltage-cables-2 series is designed for high-voltage
  applications, utilizing stranded copper conductors and XLPE insulation to
  ensure high ampacity and robust performance in industrial settings.
categories:
  - High Voltage Cables
images: []
locale: en
---
<ProductTabs technicalData={<ProductTechnicalData data={{
  "technicalItems": [
    {
      "label": "Rated voltage (kV)",
      "value": "64/110",
      "unit": "kV"
    }
  ],
  "voltageTables": [
    {
      "voltageLabel": "64/110 kV",
      "metaItems": [
        {
          "label": "Voltage",
          "value": "64/110 kV"
        }
      ],
      "columns": [
        {
          "key": "Cond",
          "label": "Cond."
        },
        {
          "key": "RI",
          "label": "RI [Ohm/km]"
        },
        {
          "key": "Wi",
          "label": "Wi [mm]"
        },
        {
          "key": "Rbv",
          "label": "Rbv [mm]"
        },
        {
          "key": "Ø",
          "label": "Ø [mm]"
        },
        {
          "key": "G",
          "label": "G [kg/km]"
        }
      ],
      "rows": [
        {
          "configuration": "1×240RM",
          "cells": [
            "Cu",
            "0.1",
            "16.5",
            "2.2",
            "86",
            "7040"
          ]
        },
        {
          "configuration": "1×300RM",
          "cells": [
            "Cu",
            "0.08",
            "15.5",
            "2.2",
            "86",
            "7550"
          ]
        },
        {
          "configuration": "1×400RM",
          "cells": [
            "Cu",
            "0.06",
            "14.5",
            "2.2",
            "88",
            "8380"
          ]
        },
        {
          "configuration": "1×500RM",
          "cells": [
            "Cu",
            "0.05",
            "14",
            "2.2",
            "91",
            "9530"
          ]
        },
        {
          "configuration": "1×630RM",
          "cells": [
            "Cu",
            "0.04",
            "14",
            "2.4",
            "95",
            "11190"
          ]
        },
        {
          "configuration": "1×800RM",
          "cells": [
            "Cu",
            "0.03",
            "14",
            "2.5",
            "100",
            "13160"
          ]
        },
        {
          "configuration": "1×1000RM",
          "cells": [
            "Cu",
            "0.03",
            "14",
            "2.6",
            "104",
            "15380"
          ]
        },
        {
          "configuration": "1×1200RMS",
          "cells": [
            "Cu",
            "0.02",
            "14",
            "2.8",
            "110",
            "17790"
          ]
        },
        {
          "configuration": "1×1400RMS",
          "cells": [
            "Cu",
            "0.02",
            "14",
            "2.9",
            "115",
            "19870"
          ]
        },
        {
          "configuration": "1×1600RMS",
          "cells": [
            "Cu",
            "0.02",
            "14",
            "3",
            "119",
            "22210"
          ]
        },
        {
          "configuration": "1×1800RMS",
          "cells": [
            "Cu",
            "0.02",
            "14",
            "3.1",
            "122",
            "24720"
          ]
        },
        {
          "configuration": "1×2000RMS",
          "cells": [
            "Cu",
            "0.02",
            "14",
            "3.1",
            "124",
            "26340"
          ]
        },
        {
          "configuration": "1×2500RMS",
          "cells": [
            "Cu",
            "0.01",
            "14.5",
            "3.3",
            "134",
            "31880"
          ]
        }
      ]
    }
  ]
}} />}>

<section>
<h2>Engineering Overview</h2>
<p>The <strong>N2X(F)KLD2Y-high-voltage-cables-2 series</strong> is engineered to meet the rigorous demands of high-voltage power transmission with a focus on durability, efficiency, and safety. This series is ideal for applications requiring high dielectric strength and excellent thermal cycling resistance.</p>
</section>
<section>
<h2>Technical Performance and Installation</h2>
<p>This cable series is designed to optimize both electrical and thermal performance, making it suitable for a variety of installation environments:</p>
<ul>
<li>High <strong>ampacity</strong> to support increased power transmission over long distances without significant power losses.</li>
<li>Excellent <strong>fault current withstand</strong> capability, ensuring reliability and safety in the event of abnormal current flow.</li>
<li>Designed for <strong>direct burial</strong>, <strong>trefoil formation</strong>, or <strong>cable tray mounting</strong>, providing flexibility in installation methods to suit different site conditions.</li>
</ul>
</section>
<section>
<h2>Compliance and EMC Considerations</h2>
<p>The cable's construction adheres to stringent <strong>IEC standards</strong> and carries the <strong>CE marking</strong>, affirming its compliance with the Construction Products Regulation (<strong>CPR classification</strong>). Furthermore, it is designed to minimize electromagnetic interference:</p>
<ul>
<li>Advanced insulation and shielding techniques reduce <strong>induced voltage</strong>, enhancing <strong>electromagnetic compatibility</strong> (EMC).</li>
<li>Metallic screens incorporated into the cable design help in mitigating external electromagnetic influences, ensuring stable and uninterrupted operation.</li>
</ul>
</section>

</ProductTabs>
