---
title: N2XS(F)2Y
sku: N2XS(F)2Y-medium-voltage-cables
description: >
  Das N2XS(F)2Y Kabel ist ein längswasserdichtes Mittelspannungskabel mit
  Kupferleiter, VPE-Isolation und widerstandsfähigem PE-Mantel. Es kombiniert
  hohe elektrische Sicherheit mit robuster Außenschicht für anspruchsvolle
  Anwendungen im Netzbetrieb.
categories:
  - Mittelspannungskabel
images:
  - /uploads/2025/01/N2XSF2Y-3-scaled.webp
locale: de
---
<ProductTabs technicalData={<ProductTechnicalData data={{
  "technicalItems": [
    {
      "label": "CPR class",
      "value": "Fca",
      "unit": ""
    },
    {
      "label": "Flame retardant",
      "value": "no",
      "unit": ""
    },
    {
      "label": "Isolationsdicke (nom.) (mm)",
      "value": "5,5",
      "unit": "mm"
    },
    {
      "label": "Manteldicke (min.) (mm)",
      "value": "2,1",
      "unit": "mm"
    },
    {
      "label": "Maximal operating conductor temperature (°C)",
      "value": "+90",
      "unit": "°C"
    },
    {
      "label": "Maximal short-circuit temperature (°C)",
      "value": "+250",
      "unit": "°C"
    },
    {
      "label": "Minimal storage temperature (°C)",
      "value": "-35",
      "unit": "°C"
    },
    {
      "label": "Minimal temperature for laying (°C)",
      "value": "-20",
      "unit": "°C"
    },
    {
      "label": "Nennspannung (kV)",
      "value": "12/20",
      "unit": "kV"
    },
    {
      "label": "Prüfspannung (kV)",
      "value": "42",
      "unit": "kV"
    },
    {
      "label": "Shape of conductor",
      "value": "RM",
      "unit": ""
    },
    {
      "label": "Temperaturbereich (°C)",
      "value": "-35-+90",
      "unit": "°C"
    }
  ],
  "voltageTables": [
    {
      "voltageLabel": "12/20 kV",
      "metaItems": [
        {
          "label": "Spannung",
          "value": "12/20 kV"
        },
        {
          "label": "Prüfspannung",
          "value": "42",
          "unit": "kV"
        },
        {
          "label": "Temperaturbereich",
          "value": "-35-+90",
          "unit": "°C"
        },
        {
          "label": "Leitertemperatur (max.)",
          "value": "+90",
          "unit": "°C"
        },
        {
          "label": "Kurzschlusstemperatur (max.)",
          "value": "+250",
          "unit": "°C"
        },
        {
          "label": "Minimale Verlegetemperatur",
          "value": "-20",
          "unit": "°C"
        },
        {
          "label": "Minimale Lagertemperatur",
          "value": "-35",
          "unit": "°C"
        },
        {
          "label": "CPR-Klasse",
          "value": "Fca",
          "unit": ""
        },
        {
          "label": "Flammhemmend",
          "value": "no",
          "unit": ""
        }
      ],
      "columns": [
        {
          "key": "Cond",
          "label": "Leiter"
        },
        {
          "key": "shape",
          "label": "Form"
        },
        {
          "key": "cap",
          "label": "Cap [uF/km]"
        },
        {
          "key": "DI",
          "label": "DI [mm]"
        },
        {
          "key": "RI",
          "label": "RI [Ohm/km]"
        },
        {
          "key": "Wi",
          "label": "Wi [mm]"
        },
        {
          "key": "Ibl",
          "label": "Ibl [A]"
        },
        {
          "key": "Ibe",
          "label": "Ibe [A]"
        },
        {
          "key": "Ik_cond",
          "label": "Ik [kA]"
        },
        {
          "key": "Wm",
          "label": "Wm [mm]"
        },
        {
          "key": "Rbv",
          "label": "Rbv [mm]"
        },
        {
          "key": "Ø",
          "label": "Ø [mm]"
        },
        {
          "key": "G",
          "label": "G [kg/km]"
        }
      ],
      "rows": [
        {
          "configuration": "1x35/16",
          "cells": [
            "Cu",
            "RM",
            "0,16",
            "19,5",
            "0,524",
            "5,5",
            "200",
            "189",
            "5",
            "2,1",
            "420",
            "28",
            "949"
          ]
        },
        {
          "configuration": "1x50/16",
          "cells": [
            "Cu",
            "RM",
            "0,17",
            "20,5",
            "0,387",
            "5,5",
            "239",
            "222",
            "7,1",
            "2,1",
            "435",
            "29",
            "1079"
          ]
        },
        {
          "configuration": "1x70/16",
          "cells": [
            "Cu",
            "RM",
            "0,19",
            "22,1",
            "0,268",
            "5,5",
            "297",
            "271",
            "10",
            "2,1",
            "465",
            "31",
            "1315"
          ]
        },
        {
          "configuration": "1x95/16",
          "cells": [
            "Cu",
            "RM",
            "0,21",
            "23,6",
            "0,193",
            "5,5",
            "361",
            "323",
            "13,6",
            "2,1",
            "480",
            "32",
            "1580"
          ]
        },
        {
          "configuration": "1x120/16",
          "cells": [
            "Cu",
            "RM",
            "0,23",
            "25,1",
            "0,153",
            "5,5",
            "416",
            "367",
            "17,1",
            "2,1",
            "510",
            "34",
            "1862"
          ]
        },
        {
          "configuration": "1x150/25",
          "cells": [
            "Cu",
            "RM",
            "0,25",
            "26,5",
            "0,124",
            "5,5",
            "470",
            "409",
            "21,4",
            "2,1",
            "525",
            "35",
            "2212"
          ]
        },
        {
          "configuration": "1x185/25",
          "cells": [
            "Cu",
            "RM",
            "0,27",
            "28,1",
            "0,099",
            "5,5",
            "538",
            "461",
            "26,4",
            "2,1",
            "555",
            "37",
            "2585"
          ]
        },
        {
          "configuration": "1x240/25",
          "cells": [
            "Cu",
            "RM",
            "0,3",
            "30,6",
            "0,075",
            "5,5",
            "634",
            "532",
            "34,3",
            "2,1",
            "585",
            "39",
            "3181"
          ]
        },
        {
          "configuration": "1x300/25",
          "cells": [
            "Cu",
            "RM",
            "0,33",
            "33",
            "0,06",
            "5,5",
            "724",
            "599",
            "42,9",
            "2,1",
            "630",
            "42",
            "3851"
          ]
        },
        {
          "configuration": "1x400/35",
          "cells": [
            "Cu",
            "RM",
            "0,36",
            "35,6",
            "0,047",
            "5,5",
            "829",
            "671",
            "57,2",
            "2,1",
            "660",
            "44",
            "4795"
          ]
        },
        {
          "configuration": "1x500/35",
          "cells": [
            "Cu",
            "RM",
            "0,4",
            "38,8",
            "0,037",
            "5,5",
            "953",
            "754",
            "71,4",
            "2,1",
            "705",
            "47",
            "5873"
          ]
        }
      ]
    }
  ]
}} />}>

<section>
<h3 data-start="452" data-end="502">Entwickelt für leistungsstarke Netzumgebungen</h3>
<p data-start="504" data-end="904">Das <strong data-start="508" data-end="521">N2XS(F)2Y</strong> erfüllt die gängigen Normen <strong data-start="550" data-end="570">DIN VDE 0276-620</strong>, <strong data-start="572" data-end="585">HD 620 S2</strong> und <strong data-start="590" data-end="603">IEC 60502</strong> und ist für die <strong data-start="620" data-end="713">Verlegung in Innenräumen, Kabelkanälen, im Freien, in Wasser, Erde und auf Kabelpritschen</strong> geeignet. Besonders in <strong data-start="737" data-end="785">EVU-Netzen, Industrieanlagen und Kraftwerken</strong> spielt dieses Kabel seine Stärken aus – überall dort, wo Langlebigkeit, Wasserdichtigkeit und Sicherheit gefragt sind.</p>
<h3 data-start="906" data-end="946">Aufbau und technische Eigenschaften</h3>
<p data-start="948" data-end="1387">Im Inneren befindet sich ein <strong data-start="977" data-end="1016">blanker, mehrdrähtiger Kupferleiter</strong> (Klasse 2), umgeben von einer <strong data-start="1047" data-end="1123">extrudierten VPE-Isolation mit innerer und haftender äußerer Leitschicht</strong>. Eine <strong data-start="1130" data-end="1174">längswasserdichte, leitfähige Bandierung</strong>, eine <strong data-start="1181" data-end="1234">Abschirmung aus Kupferdrähten mit Querleitwendeln</strong> und eine zusätzliche <strong data-start="1256" data-end="1282">längswasserdichte Lage</strong> sichern den Aufbau. Der schwarze <strong data-start="1316" data-end="1345">PE-Außenmantel (Typ DMP2)</strong> sorgt für hohe mechanische Belastbarkeit.</p>
<h3 data-start="1389" data-end="1425">Anwendungsbereiche und Vorteile</h3>
<p data-start="1427" data-end="1822">Das N2XS(F)2Y ist <strong data-start="1445" data-end="1461">erdverlegbar</strong>, <strong data-start="1463" data-end="1509">resistent gegen aggressive Umwelteinflüsse</strong> und hält <strong data-start="1519" data-end="1562">Temperaturen bis +90 °C im Dauerbetrieb</strong> sowie <strong data-start="1569" data-end="1599">+250 °C im Kurzschlussfall</strong> stand. Es ist <strong data-start="1614" data-end="1663">frei von silikon- und cadmiumhaltigen Stoffen</strong> und dank des <strong data-start="1677" data-end="1709">teilentladungsfreien Aufbaus</strong> besonders geeignet für Netze mit höchsten Anforderungen an <strong data-start="1769" data-end="1803">elektrische Betriebssicherheit</strong> und Langlebigkeit.</p>
</section>

</ProductTabs>
