../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-vendor-DOMPurify-DOMPurify.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-assets-js-external-permalinks.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-js-front-end-breeze-prefetch-links.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-jquery-jquery.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-jquery-jquery-migrate.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-min-svgs-inline-vanilla-min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-zoom-jquery.zoom.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-photoswipe-photoswipe.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-photoswipe-photoswipe-ui-default.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-frontend-single-product.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-jquery-blockui-jquery.blockUI.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-js-cookie-js.cookie.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-frontend-woocommerce.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-dist-scripts-url-shortify.js
Skip to main content
Hit enter to search or ESC to close
Close Search

# N2XSY

The N2XSY cable is a high-performance medium-voltage cable with a copper conductor, XLPE insulation, and a PVC sheath. It offers excellent electrical characteristics and can be installed safely and efficiently, even in complex routing situations.

Request Cable
Email *
Request *
If you are human, leave this field blank.
SKU: N2XSY-medium-voltage-cables Category: Medium Voltage Cables

- Description

## Description

### For powerful medium-voltage applications

The N2XSY meets the standards DIN VDE 0276-620, HD 620 S2 and IEC 60502. It is designed for installation indoors, in cable ducts, in water, underground, or outdoors (when protected). Whether in industrial plants, power stations, or substations – this cable ensures safe and low-loss power transmission in medium-voltage networks.

### Construction and technical features

The cable consists of a bare, multi-stranded copper conductor (Class 2), surrounded by XLPE insulation with a tightly bonded outer conductive layer. A conductive tape, a copper wire screen with counter helix, additional tape, and a red PVC sheath (Type DMV6) complete the construction. The extruded combination of insulation and conductive layer ensures partial discharge-free operation and high reliability.

### Properties and application benefits

The N2XSY cable is suitable for underground installation, flame-retardant according to DIN VDE 0482-332-1-2, and free from silicone and cadmium-containing substances. With a +90 °C operating temperature and +250 °C short-circuit resistance, it is ideal for networks with high thermal loads. Excellent installation properties also allow for easy handling, even in complex routing scenarios.

## Datasheet

Configuration | Rated Voltage | Test Voltage | Maximal Short Circuit Temperature | Maximal Operating Conductor Temperature | Minimal Temperature For Laying | Operating Temperature Range | Colour Of Sheath | Packaging | RoHS/REACH | Bending Radius
--- | --- | --- | --- | --- | --- | --- | --- | --- | --- | ---
1x35/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 360 mm
1x50/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 390 mm
1x70/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 405 mm
1x95/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 435 mm
1x120/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 450 mm
1x150/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 480 mm
1x185/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 495 mm
1x240/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 540 mm
1x300/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 570 mm
1x400/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 615 mm
1x500/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 660 mm
1x35/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 435 mm
1x50/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 450 mm
1x70/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 465 mm
1x95/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 495 mm
1x120/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 510 mm
1x150/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 540 mm
1x185/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 555 mm
1x240/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 600 mm
1x300/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 630 mm
1x400/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 675 mm
1x500/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 720 mm
1x50/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 525 mm
1x70/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 540 mm
1x95/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 570 mm
1x120/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 585 mm
1x150/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 615 mm
1x185/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 630 mm
1x240/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 675 mm
1x300/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 705 mm
1x400/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 750 mm
1x500/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -5 °C | -35 - +90 °C | red or black | wooden or metal drums | N/A | 795 mm

### Other Specifications

Configuration | Conductor | Insulation | Conductive Tape Below Screen | Copper Wire Screen And Tape | Non Conducting Tape Above Screen | Al Foil | Sheath | Number Of Cores And Cross Section | Minimal Storage Temperature | Colour Of Insulation | Flame Retardant | CPR Class | CE Conformity | Shape Of Conductor | Conductor Diameter | Nominal Insulation Thickness | Diameter Over Insulation | Minimum Sheath Thickness | Outer Diameter | Weight | DC Resistance At 20 °C | Capacitance | Inductance, Trefoil | Inductance In Ground, Flat 1 | Conductor Shortcircuit Current | Screen Shortcircuit Current | Heating Time Constant, Trefoil | Heating Time Constant, Flat | Current Ratings In Air, Trefoil | Current Ratings In Air, Flat | Current Ratings In Ground, Trefoil | Current Ratings In Ground, Flat
--- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | ---
1x35/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x35/16 | –25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 7.2 mm | 3.4 mm | 15.3 mm | 2.1 mm | 24 mm | 904 kg/km | 0.524 Ω/km | 0.22 μF/km | 0.43 | 0.73 | 5 kA | 3.2 kA | 275 | 198 | 197 | 235 | 187 | 212
1x50/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x50/16 | –25 °C | uncoloured | EN 60 332-1-3 | Eca | yes | RM | 8.2 mm | 3.4 mm | 16.3 mm | 2.1 mm | 26 mm | 1039 kg/km | 0.387 Ω/km | 0.24 μF/km | 0.42 | 0.71 | 7.1 kA | 3.2 kA | 387 | 281 | 238 | 282 | 220 | 249
1x70/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x70/16 | –25 °C | uncoloured | EN 60 332-1-4 | Eca | yes | RM | 9.8 mm | 3.4 mm | 17.9 mm | 2.1 mm | 27 mm | 1271 kg/km | 0.268 Ω/km | 0.28 μF/km | 0.39 | 0.67 | 10 kA | 3.2 kA | 503 | 368 | 294 | 350 | 268 | 302
1x95/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x95/16 | –25 °C | uncoloured | EN 60 332-1-5 | Eca | yes | RM | 11.3 mm | 3.4 mm | 19.4 mm | 2.1 mm | 29 mm | 1530 kg/km | 0.193 Ω/km | 0.3 μF/km | 0.38 | 0.65 | 13.6 kA | 3.2 kA | 630 | 465 | 358 | 426 | 320 | 359
1x120/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x120/16 | –25 °C | uncoloured | EN 60 332-1-6 | Eca | yes | RM | 12.8 mm | 3.4 mm | 20.9 mm | 2.1 mm | 30 mm | 1809 kg/km | 0.153 Ω/km | 0.34 μF/km | 0.36 | 0.62 | 17.1 kA | 3.2 kA | 763 | 569 | 413 | 491 | 363 | 405
1x150/25 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x150/25 | –25 °C | uncoloured | EN 60 332-1-7 | Eca | yes | RM | 14.2 mm | 3.4 mm | 22.3 mm | 2.1 mm | 32 mm | 2158 kg/km | 0.124 Ω/km | 0.36 μF/km | 0.35 | 0.6 | 21.4 kA | 5 kA | 948 | 743 | 468 | 549 | 405 | 442
1x185/25 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x185/25 | –25 °C | uncoloured | EN 60 332-1-8 | Eca | yes | RM | 15.8 mm | 3.4 mm | 23.9 mm | 2.1 mm | 33 mm | 2524 kg/km | 0.099 Ω/km | 0.4 μF/km | 0.34 | 0.58 | 26.4 kA | 5 kA | 1125 | 897 | 535 | 625 | 456 | 493
1x240/25 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x240/25 | –25 °C | uncoloured | EN 60 332-1-9 | Eca | yes | RM | 18.3 mm | 3.4 mm | 26.4 mm | 2.1 mm | 36 mm | 3117 kg/km | 0.075 Ω/km | 0.44 μF/km | 0.32 | 0.55 | 34.3 kA | 5 kA | 1370 | 1135 | 631 | 731 | 526 | 563
1x300/25 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x300/25 | –25 °C | uncoloured | EN 60 332-1-10 | Eca | yes | RM | 20.7 mm | 3.4 mm | 28.8 mm | 2.1 mm | 38 mm | 3786 kg/km | 0.06 Ω/km | 0.49 μF/km | 0.31 | 0.53 | 42.9 kA | 5 kA | 1636 | 1377 | 722 | 831 | 591 | 626
1x400/35 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x400/35 | –25 °C | uncoloured | EN 60 332-1-11 | Eca | yes | RM | 23.3 mm | 3.4 mm | 31.4 mm | 2.1 mm | 41 mm | 4750 kg/km | 0.047 Ω/km | 0.54 μF/km | 0.29 | 0.5 | 57.2 kA | 7 kA | 2352 | 2133 | 827 | 920 | 662 | 675
1x500/35 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x500/35 | –25 °C | uncoloured | EN 60 332-1-12 | Eca | yes | RM | 26.5 mm | 3.4 mm | 34.6 mm | 2.1 mm | 44 mm | 5786 kg/km | 0.037 Ω/km | 0.61 μF/km | 0.28 | 0.48 | 71.4 kA | 7 kA | 2917 | 2727 | 949 | 1043 | 744 | 748
1x35/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x35/16 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 7.2 mm | 5.5 mm | 19.5 mm | 2.1 mm | 29 mm | 1069 kg/km | 0.524 Ω/km | 0.16 μF/km | 0.46 | 0.74 | 5 kA | 3.2 kA | 266 | 199 | 200 | 235 | 189 | 213
1x50/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x50/16 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 8.2 mm | 5.5 mm | 20.5 mm | 2.1 mm | 30 mm | 1203 kg/km | 0.387 Ω/km | 0.17 μF/km | 0.45 | 0.72 | 7.1 kA | 3.2 kA | 383 | 288 | 239 | 282 | 222 | 250
1x70/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x70/16 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 9.8 mm | 5.5 mm | 22.1 mm | 2.1 mm | 31 mm | 1447 kg/km | 0.268 Ω/km | 0.19 μF/km | 0.42 | 0.68 | 10 kA | 3.2 kA | 489 | 371 | 297 | 351 | 271 | 303
1x95/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x95/16 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 11.3 mm | 5.5 mm | 23.6 mm | 2.1 mm | 33 mm | 1718 kg/km | 0.193 Ω/km | 0.21 μF/km | 0.4 | 0.66 | 13.6 kA | 3.2 kA | 613 | 470 | 361 | 426 | 323 | 360
1x120/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x120/16 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 12.8 mm | 5.5 mm | 25.1 mm | 2.1 mm | 34 mm | 2007 kg/km | 0.153 Ω/km | 0.23 μF/km | 0.39 | 0.63 | 17.1 kA | 3.2 kA | 742 | 574 | 416 | 491 | 367 | 407
1x150/25 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x150/25 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 14.2 mm | 5.5 mm | 26.5 mm | 2.1 mm | 36 mm | 2364 kg/km | 0.124 Ω/km | 0.25 μF/km | 0.37 | 0.6 | 21.4 kA | 5 kA | 920 | 747 | 470 | 549 | 409 | 445
1x185/25 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x185/25 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 15.8 mm | 5.5 mm | 28.1 mm | 2.1 mm | 37 mm | 2744 kg/km | 0.099 Ω/km | 0.27 μF/km | 0.36 | 0.59 | 26.4 kA | 5 kA | 1079 | 892 | 538 | 625 | 461 | 498
1x240/25 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x240/25 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 18.3 mm | 5.5 mm | 30.6 mm | 2.1 mm | 40 mm | 3352 kg/km | 0.075 Ω/km | 0.3 μF/km | 0.34 | 0.56 | 34.3 kA | 5 kA | 1344 | 1143 | 634 | 731 | 532 | 568
1x300/25 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x300/25 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 20.7 mm | 5.5 mm | 33 mm | 2.1 mm | 42 mm | 4032 kg/km | 0.06 Ω/km | 0.35 μF/km | 0.33 | 0.54 | 42.9 kA | 5 kA | 1582 | 1364 | 724 | 830 | 599 | 633
1x400/35 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x400/35 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 23.3 mm | 5.5 mm | 35.6 mm | 2.1 mm | 45 mm | 4988 kg/km | 0.047 Ω/km | 0.36 μF/km | 0.31 | 0.51 | 57.2 kA | 7 kA | 2327 | 2182 | 829 | 923 | 671 | 685
1x500/35 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x500/35 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 26.5 mm | 5.5 mm | 38.8 mm | 2.1 mm | 48 mm | 6080 kg/km | 0.037 Ω/km | 0.43 μF/km | 0.3 | 0.49 | 71.4 kA | 7 kA | 2765 | 2689 | 953 | 1045 | 754 | 760
1x50/16 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x50/16 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 8.2 mm | 8 mm | 25.5 mm | 2.1 mm | 35 mm | 1439 kg/km | 0.387 Ω/km | 0.13 μF/km | 0.48 | 0.73 | 7.1 kA | 3.2 kA | 367 | 288 | 241 | 282 | 225 | 251
1x70/16 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x70/16 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 9.8 mm | 8 mm | 27.1 mm | 2.1 mm | 36 mm | 1697 kg/km | 0.268 Ω/km | 0.15 μF/km | 0.45 | 0.7 | 10 kA | 3.2 kA | 476 | 374 | 299 | 350 | 274 | 304
1x95/16 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x95/16 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 11.3 mm | 8 mm | 28.6 mm | 2.1 mm | 38 mm | 1979 kg/km | 0.193 Ω/km | 0.16 μF/km | 0.43 | 0.67 | 13.6 kA | 3.2 kA | 598 | 476 | 363 | 425 | 327 | 362
1x120/16 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x120/16 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 12.8 mm | 8 mm | 30.1 mm | 2.1 mm | 39 mm | 2279 kg/km | 0.153 Ω/km | 0.17 μF/km | 0.41 | 0.64 | 17.1 kA | 3.2 kA | 729 | 585 | 418 | 468 | 371 | 409
1x150/25 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x150/25 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 14.2 mm | 8 mm | 31.5 mm | 2.1 mm | 41 mm | 2648 kg/km | 0.124 Ω/km | 0.19 μF/km | 0.4 | 0.62 | 21.4 kA | 5 kA | 910 | 760 | 472 | 548 | 414 | 449
1x185/25 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x185/25 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 15.8 mm | 8 mm | 33.1 mm | 2.1 mm | 42 mm | 3036 kg/km | 0.099 Ω/km | 0.2 μF/km | 0.38 | 0.6 | 26.4 kA | 5 kA | 1073 | 913 | 539 | 624 | 466 | 502
1x240/25 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x240/25 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 18.3 mm | 8 mm | 35.6 mm | 2.1 mm | 45 mm | 3661 kg/km | 0.075 Ω/km | 0.22 μF/km | 0.36 | 0.57 | 34.3 kA | 5 kA | 1318 | 1143 | 635 | 728 | 539 | 574
1x300/25 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x300/25 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 20.7 mm | 8 mm | 38 mm | 2.1 mm | 47 mm | 4368 kg/km | 0.06 Ω/km | 0.24 μF/km | 0.35 | 0.55 | 42.9 kA | 5 kA | 1595 | 1405 | 725 | 828 | 606 | 640
1x400/35 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x400/35 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 23.3 mm | 8 mm | 40.6 mm | 2.1 mm | 50 mm | 5347 kg/km | 0.047 Ω/km | 0.26 μF/km | 0.34 | 0.52 | 57.2 kA | 7 kA | 2255 | 2182 | 831 | 922 | 680 | 695
1x500/35 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PVC | 1x500/35 | -25 °C | uncoloured | EN 60 332-1-2 | Eca | yes | RM | 26.5 mm | 8 mm | 43.8 mm | 2.4 mm | 53 mm | 6472 kg/km | 0.037 Ω/km | 0.29 μF/km | 0.32 | 0.5 | 71.4 kA | 7 kA | 2727 | 2727 | 953 | 1045 | 765 | 773

## Related products

- ## N2XS2Y

- ## N2XS(F)2Y

- ## NA2XS(FL)2Y

- ## N2XS(FL)2Y

Share Share Share Pin
Close Menu

#### KLZ Cables

Raiffeisenstraße 22
73630 Remshalden

[email protected]

../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-salient-social-js-salient-social.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-build-third-party-jquery.easing.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-build-third-party-jquery.mousewheel.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-build-priority.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-build-third-party-transit.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-build-third-party-waypoints.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-build-third-party-imagesLoaded.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-build-third-party-hoverintent.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-build-third-party-jquery.fancybox.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-build-third-party-anime.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-build-third-party-superfish.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-build-init.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-build-nectar-smooth-scroll.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-build-third-party-flickity.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-build-nectar-single-product.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-third-party-touchswipe.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-js-front-end-breeze-lazy-load.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-sourcebuster-sourcebuster.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-frontend-order-attribution.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-build-nectar-delay-javascript.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-formidable-pro-js-frm.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-dist-hooks.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsy-1-44063-js-build-gtag-events.js