../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-vendor-DOMPurify-DOMPurify.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-assets-js-external-permalinks.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-js-front-end-breeze-prefetch-links.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-jquery-jquery.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-jquery-jquery-migrate.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-min-svgs-inline-vanilla-min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-zoom-jquery.zoom.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-photoswipe-photoswipe.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-photoswipe-photoswipe-ui-default.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-frontend-single-product.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-jquery-blockui-jquery.blockUI.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-js-cookie-js.cookie.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-frontend-woocommerce.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-dist-scripts-url-shortify.js
Skip to main content
Hit enter to search or ESC to close
Close Search

# N2XS2Y

The N2XS2Y cable is a robust medium-voltage cable with a copper conductor, XLPE insulation, and a durable PE sheath. It ensures reliable power transmission even under high mechanical stress and demanding environmental conditions.

Request Cable
Email *
Request *
If you are human, leave this field blank.
SKU: N2XS2Y-medium-voltage-cables Category: Medium Voltage Cables

- Description

## Description

### For underground installation and demanding environments

The N2XS2Y complies with the standards DIN VDE 0276-620, HD 620 S2 and IEC 60502. It is suitable for installation indoors, in cable ducts, outdoors, in water, on cable trays, and especially underground. Thanks to its robust sheath, it is frequently used in industrial plants, power stations, and switching stations, where stability and durability are essential.

### Technical construction

The conductor consists of bare, multi-stranded copper (Class 2), surrounded by an inner conductive layer and XLPE insulation with a tightly bonded outer conductive layer. The shielding is provided by a copper wire braid with counter helix. Additionally, the cable includes a conductive tape and features a black PE sheath (Type DMP2) that protects against moisture and mechanical abrasion.

### Features and application benefits

The N2XS2Y is suitable for underground installation, free from silicone and cadmium, and not flame-retardant. It is rated for +90 °C in operation and +250 °C under short-circuit conditions. Thanks to its partial discharge-free design, it offers a high level of safety and is particularly well-suited for networks with heavy load and challenging routing conditions.

## Datasheet

Configuration | Rated Voltage | Test Voltage | Maximal Short Circuit Temperature | Maximal Operating Conductor Temperature | Minimal Temperature For Laying | Operating Temperature Range | Colour Of Sheath | Packaging | RoHS/REACH | Bending Radius
--- | --- | --- | --- | --- | --- | --- | --- | --- | --- | ---
1x35/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 360 mm
1x50/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 375 mm
1x70/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 390 mm
1x95/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 420 mm
1x120/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 450 mm
1x150/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 465 mm
1x185/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 480 mm
1x240/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 525 mm
1x300/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 555 mm
1x400/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 600 mm
1x500/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 645 mm
1x35/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 420 mm
1x50/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 435 mm
1x70/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 465 mm
1x95/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 480 mm
1x120/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 510 mm
1x150/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 525 mm
1x185/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 555 mm
1x240/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 585 mm
1x300/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 630 mm
1x400/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 660 mm
1x500/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 705 mm
1x50/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 510 mm
1x70/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 540 mm
1x95/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 555 mm
1x120/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 585 mm
1x150/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 600 mm
1x185/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 630 mm
1x240/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 660 mm
1x300/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 705 mm
1x400/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 735 mm
1x500/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 795 mm

### Other Specifications

Configuration | Conductor | Insulation | Conductive Tape Below Screen | Copper Wire Screen And Tape | Non Conducting Tape Above Screen | Al Foil | Sheath | Number Of Cores And Cross Section | Minimal Storage Temperature | Colour Of Insulation | Flame Retardant | CPR Class | CE Conformity | Shape Of Conductor | Conductor Diameter | Nominal Insulation Thickness | Diameter Over Insulation | Minimum Sheath Thickness | Outer Diameter | Weight | DC Resistance At 20 °C | Capacitance | Inductance, Trefoil | Inductance In Ground, Flat 1 | Conductor Shortcircuit Current | Screen Shortcircuit Current | Heating Time Constant, Trefoil | Heating Time Constant, Flat | Current Ratings In Air, Trefoil | Current Ratings In Air, Flat | Current Ratings In Ground, Trefoil | Current Ratings In Ground, Flat
--- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | ---
1x35/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x35/16 | –35 °C | uncoloured | no | Fca | yes | RM | 7.2 mm | 3.4 mm | 15.3 mm | 2.1 mm | 24 mm | 803 kg/km | 0.524 Ω/km | 0.22 μF/km | 0.43 | 0.73 | 5 kA | 3.2 kA | 267 | 190 | 197 | 235 | 187 | 212
1x50/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x50/16 | –35 °C | uncoloured | no | Fca | yes | RM | 8.2 mm | 3.4 mm | 16.3 mm | 2.1 mm | 25 mm | 928 kg/km | 0.387 Ω/km | 0.24 μF/km | 0.42 | 0.71 | 7.1 kA | 3.2 kA | 375 | 269 | 238 | 282 | 220 | 249
1x70/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x70/16 | –35 °C | uncoloured | no | Fca | yes | RM | 9.8 mm | 3.4 mm | 17.9 mm | 2.1 mm | 26 mm | 1154 kg/km | 0.268 Ω/km | 0.28 μF/km | 0.39 | 0.67 | 10 kA | 3.2 kA | 488 | 352 | 294 | 350 | 268 | 302
1x95/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x95/16 | –35 °C | uncoloured | no | Fca | yes | RM | 11.3 mm | 3.4 mm | 19.4 mm | 2.1 mm | 28 mm | 1410 kg/km | 0.193 Ω/km | 0.3 μF/km | 0.38 | 0.65 | 13.6 kA | 3.2 kA | 611 | 446 | 358 | 426 | 320 | 359
1x120/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x120/16 | –35 °C | uncoloured | no | Fca | yes | RM | 12.8 mm | 3.4 mm | 20.9 mm | 2.1 mm | 30 mm | 1682 kg/km | 0.153 Ω/km | 0.34 μF/km | 0.36 | 0.62 | 17.1 kA | 3.2 kA | 742 | 545 | 413 | 491 | 363 | 405
1x150/25 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x150/25 | –35 °C | uncoloured | no | Fca | yes | RM | 14.2 mm | 3.4 mm | 22.3 mm | 2.1 mm | 31 mm | 2025 kg/km | 0.124 Ω/km | 0.36 μF/km | 0.35 | 0.6 | 21.4 kA | 5 kA | 917 | 709 | 468 | 549 | 405 | 442
1x185/25 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x185/25 | –35 °C | uncoloured | no | Fca | yes | RM | 15.8 mm | 3.4 mm | 23.9 mm | 2.1 mm | 32 mm | 2383 kg/km | 0.099 Ω/km | 0.4 μF/km | 0.34 | 0.58 | 26.4 kA | 5 kA | 1089 | 861 | 535 | 625 | 456 | 493
1x240/25 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x240/25 | –35 °C | uncoloured | no | Fca | yes | RM | 18.3 mm | 3.4 mm | 26.4 mm | 2.1 mm | 35 mm | 2965 kg/km | 0.075 Ω/km | 0.44 μF/km | 0.32 | 0.55 | 34.3 kA | 5 kA | 1318 | 1073 | 631 | 731 | 526 | 563
1x300/25 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x300/25 | –35 °C | uncoloured | no | Fca | yes | RM | 20.7 mm | 3.4 mm | 28.8 mm | 2.1 mm | 37 mm | 3624 kg/km | 0.06 Ω/km | 0.49 μF/km | 0.31 | 0.53 | 42.9 kA | 5 kA | 1582 | 1309 | 722 | 831 | 591 | 626
1x400/35 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x400/35 | –35 °C | uncoloured | no | Fca | yes | RM | 23.3 mm | 3.4 mm | 31.4 mm | 2.1 mm | 40 mm | 4574 kg/km | 0.047 Ω/km | 0.54 μF/km | 0.29 | 0.5 | 57.2 kA | 7 kA | 2279 | 2036 | 827 | 920 | 662 | 675
1x500/35 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x500/35 | –35 °C | uncoloured | no | Fca | yes | RM | 26.5 mm | 3.4 mm | 34.6 mm | 2.1 mm | 43 mm | 5597 kg/km | 0.037 Ω/km | 0.61 μF/km | 0.28 | 0.48 | 71.4 kA | 7 kA | 2765 | 2538 | 949 | 1043 | 744 | 748
1x35/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x35/16 | -35 °C | uncoloured | no | Fca | yes | RM | 7.2 mm | 5.5 mm | 19.5 mm | 2.1 mm | 28 mm | 948 kg/km | 0.524 Ω/km | 0.16 μF/km | 0.46 | 0.74 | 5 kA | 3.2 kA | 259 | 192 | 200 | 235 | 189 | 213
1x50/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x50/16 | -35 °C | uncoloured | no | Fca | yes | RM | 8.2 mm | 5.5 mm | 20.5 mm | 2.1 mm | 29 mm | 1078 kg/km | 0.387 Ω/km | 0.17 μF/km | 0.44 | 0.72 | 7.1 kA | 3.2 kA | 373 | 278 | 239 | 282 | 222 | 250
1x70/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x70/16 | -35 °C | uncoloured | no | Fca | yes | RM | 9.8 mm | 5.5 mm | 22.1 mm | 2.1 mm | 31 mm | 1315 kg/km | 0.268 Ω/km | 0.19 μF/km | 0.42 | 0.68 | 10 kA | 3.2 kA | 476 | 358 | 297 | 351 | 271 | 303
1x95/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x95/16 | -35 °C | uncoloured | no | Fca | yes | RM | 11.3 mm | 5.5 mm | 23.6 mm | 2.1 mm | 32 mm | 1579 kg/km | 0.193 Ω/km | 0.21 μF/km | 0.4 | 0.66 | 13.6 kA | 3.2 kA | 598 | 454 | 361 | 426 | 323 | 360
1x120/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x120/16 | -35 °C | uncoloured | no | Fca | yes | RM | 12.8 mm | 5.5 mm | 25.1 mm | 2.1 mm | 34 mm | 1861 kg/km | 0.153 Ω/km | 0.23 μF/km | 0.39 | 0.63 | 17.1 kA | 3.2 kA | 722 | 554 | 416 | 491 | 367 | 407
1x150/25 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x150/25 | -35 °C | uncoloured | no | Fca | yes | RM | 14.2 mm | 5.5 mm | 26.5 mm | 2.1 mm | 35 mm | 2212 kg/km | 0.124 Ω/km | 0.25 μF/km | 0.37 | 0.6 | 21.4 kA | 5 kA | 897 | 723 | 470 | 549 | 409 | 445
1x185/25 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x185/25 | -35 °C | uncoloured | no | Fca | yes | RM | 15.8 mm | 5.5 mm | 28.1 mm | 2.1 mm | 37 mm | 2585 kg/km | 0.099 Ω/km | 0.27 μF/km | 0.36 | 0.59 | 26.4 kA | 5 kA | 1048 | 861 | 538 | 625 | 461 | 498
1x240/25 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x240/25 | -35 °C | uncoloured | no | Fca | yes | RM | 18.3 mm | 5.5 mm | 30.6 mm | 2.1 mm | 39 mm | 3181 kg/km | 0.075 Ω/km | 0.3 μF/km | 0.34 | 0.56 | 34.3 kA | 5 kA | 1283 | 1073 | 634 | 731 | 532 | 568
1x300/25 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x300/25 | -35 °C | uncoloured | no | Fca | yes | RM | 20.7 mm | 5.5 mm | 33 mm | 2.1 mm | 42 mm | 3763 kg/km | 0.06 Ω/km | 0.33 μF/km | 0.33 | 0.54 | 42.9 kA | 5 kA | 1541 | 1309 | 724 | 830 | 599 | 633
1x400/35 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x400/35 | -35 °C | uncoloured | no | Fca | yes | RM | 23.3 mm | 5.5 mm | 35.6 mm | 2.1 mm | 44 mm | 4795 kg/km | 0.047 Ω/km | 0.36 μF/km | 0.31 | 0.51 | 57.2 kA | 7 kA | 2279 | 2085 | 829 | 923 | 671 | 685
1x500/35 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x500/35 | -35 °C | uncoloured | no | Fca | yes | RM | 26.5 mm | 5.5 mm | 38.8 mm | 2.1 mm | 47 mm | 5872 kg/km | 0.037 Ω/km | 0.43 μF/km | 0.3 | 0.49 | 71.4 kA | 7 kA | 2689 | 2576 | 953 | 1045 | 754 | 760
1x50/16 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x50/16 | -35 °C | uncoloured | no | Fca | yes | RM | 8.2 mm | 8 mm | 25.5 mm | 2.1 mm | 34 mm | 1292 kg/km | 0.387 Ω/km | 0.13 μF/km | 0.48 | 0.73 | 7.1 kA | 3.2 kA | 359 | 280 | 241 | 282 | 225 | 251
1x70/16 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x70/16 | -35 °C | uncoloured | no | Fca | yes | RM | 9.8 mm | 8 mm | 27.1 mm | 2.1 mm | 36 mm | 1542 kg/km | 0.268 Ω/km | 0.15 μF/km | 0.45 | 0.7 | 10 kA | 3.2 kA | 466 | 364 | 299 | 350 | 274 | 304
1x95/16 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x95/16 | -35 °C | uncoloured | no | Fca | yes | RM | 11.3 mm | 8 mm | 28.6 mm | 2.1 mm | 37 mm | 1817 kg/km | 0.193 Ω/km | 0.16 μF/km | 0.43 | 0.67 | 13.6 kA | 3.2 kA | 585 | 462 | 363 | 425 | 327 | 362
1x120/16 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x120/16 | -35 °C | uncoloured | no | Fca | yes | RM | 12.8 mm | 8 mm | 30.1 mm | 2.1 mm | 39 mm | 2110 kg/km | 0.153 Ω/km | 0.17 μF/km | 0.41 | 0.64 | 17.1 kA | 3.2 kA | 711 | 567 | 418 | 468 | 371 | 409
1x150/25 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x150/25 | -35 °C | uncoloured | no | Fca | yes | RM | 14.2 mm | 8 mm | 31.5 mm | 2.1 mm | 40 mm | 2473 kg/km | 0.124 Ω/km | 0.19 μF/km | 0.4 | 0.62 | 21.4 kA | 5 kA | 890 | 740 | 472 | 548 | 414 | 449
1x185/25 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x185/25 | -35 °C | uncoloured | no | Fca | yes | RM | 15.8 mm | 8 mm | 33.1 mm | 2.1 mm | 42 mm | 2853 kg/km | 0.099 Ω/km | 0.2 μF/km | 0.38 | 0.6 | 26.4 kA | 5 kA | 1048 | 882 | 539 | 624 | 466 | 502
1x240/25 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x240/25 | -35 °C | uncoloured | no | Fca | yes | RM | 18.3 mm | 8 mm | 35.6 mm | 2.1 mm | 44 mm | 3467 kg/km | 0.075 Ω/km | 0.22 μF/km | 0.36 | 0.57 | 34.3 kA | 5 kA | 1283 | 1108 | 635 | 728 | 539 | 574
1x300/25 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x300/25 | -35 °C | uncoloured | no | Fca | yes | RM | 20.7 mm | 8 mm | 38 mm | 2.1 mm | 47 mm | 4164 kg/km | 0.06 Ω/km | 0.24 μF/km | 0.35 | 0.55 | 42.9 kA | 5 kA | 1555 | 1364 | 725 | 828 | 606 | 640
1x400/35 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x400/35 | -35 °C | uncoloured | no | Fca | yes | RM | 23.3 mm | 8 mm | 40.6 mm | 2.1 mm | 49 mm | 5131 kg/km | 0.047 Ω/km | 0.26 μF/km | 0.34 | 0.52 | 57.2 kA | 7 kA | 2206 | 2109 | 831 | 922 | 680 | 695
1x500/35 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x500/35 | -35 °C | uncoloured | no | Fca | yes | RM | 26.5 mm | 8 mm | 43.8 mm | 2.4 mm | 53 mm | 6234 kg/km | 0.037 Ω/km | 0.29 μF/km | 0.32 | 0.5 | 71.4 kA | 7 kA | 2689 | 2652 | 953 | 1045 | 765 | 773

## Related products

- ## N2XSY

- ## NA2XS(F)2Y

- ## NA2XS2Y

- ## NA2XSY

Share Share Share Pin
Close Menu

#### KLZ Cables

Raiffeisenstraße 22
73630 Remshalden

[email protected]

../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-salient-social-js-salient-social.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-build-third-party-jquery.easing.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-build-third-party-jquery.mousewheel.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-build-priority.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-build-third-party-transit.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-build-third-party-waypoints.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-build-third-party-imagesLoaded.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-build-third-party-hoverintent.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-build-third-party-jquery.fancybox.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-build-third-party-anime.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-build-third-party-superfish.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-build-init.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-build-nectar-smooth-scroll.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-build-third-party-flickity.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-build-nectar-single-product.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-third-party-touchswipe.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-js-front-end-breeze-lazy-load.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-sourcebuster-sourcebuster.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-frontend-order-attribution.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-build-nectar-delay-javascript.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-formidable-pro-js-frm.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-dist-hooks.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xs2y-1-44193-js-build-gtag-events.js