../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-vendor-DOMPurify-DOMPurify.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-assets-js-external-permalinks.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-js-front-end-breeze-prefetch-links.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-jquery-jquery.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-jquery-jquery-migrate.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-min-svgs-inline-vanilla-min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-zoom-jquery.zoom.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-photoswipe-photoswipe.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-photoswipe-photoswipe-ui-default.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-frontend-single-product.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-jquery-blockui-jquery.blockUI.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-js-cookie-js.cookie.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-frontend-woocommerce.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-dist-scripts-url-shortify.js
Skip to main content
Hit enter to search or ESC to close
Close Search

# NA2XS(FL)2Y

The NA2XS(FL)2Y cable is a longitudinally watertight medium-voltage cable with an aluminium conductor, XLPE insulation, and a combined Al/PE sheath. It has been specifically developed for power supply networks that demand high mechanical strength and reliable protection against water ingress.

Request Cable
Email *
Request *
If you are human, leave this field blank.
SKU: NA2XS(FL)2Y-medium-voltage-cables Category: Medium Voltage Cables

- Description

## Description

### Designed for use in power supply networks

The NA2XS(FL)2Y complies with standards DIN VDE 0276-620, HD 620 S2 and IEC 60502. It is ideal for installation in power supply networks (utilities), indoors, in cable ducts, outdoors, in soil, and in water. Thanks to its longitudinally watertight design and Al/PE sheath construction, it remains operational even when damaged – water ingress is effectively limited to the affected area.

### Technical construction

The cable features a multi-stranded aluminium conductor (Class 2 according to VDE 0295 / IEC 60228), surrounded by XLPE insulation with a tightly bonded outer conductive layer. A conductive, longitudinally watertight tape and a copper wire screen with counter helix ensure reliable field control. The cable is also equipped with a longitudinally watertight aluminum tape that is laminated to the black PE sheath. The result: high protection against mechanical stress and moisture ingress.

### Properties and applications

The NA2XS(FL)2Y cable is suitable for underground installation, free from silicone and cadmium, and suited for environments with high mechanical stress. It withstands temperatures up to +90 °C in operation and up to +250 °C under short-circuit conditions. Thanks to its partial discharge-free design and water barrier, it is particularly well suited for critical supply areas in power infrastructure.

## Datasheet

Configuration | Rated Voltage | Test Voltage | Maximal Short Circuit Temperature | Maximal Operating Conductor Temperature | Minimal Temperature For Laying | Operating Temperature Range | Colour Of Sheath | Packaging | RoHS/REACH | Bending Radius
--- | --- | --- | --- | --- | --- | --- | --- | --- | --- | ---
1x35/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 500 mm
1x50/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 520 mm
1x70/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 405 mm
1x95/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 580 mm
1x120/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 600 mm
1x150/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 640 mm
1x185/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 660 mm
1x240/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 720 mm
1x300/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 760 mm
1x400/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 820 mm
1x500/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 880 mm
1x630/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 940 mm
1x800/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 1040 mm
1x1000/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 1120 mm
1x50/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 600 mm
1x70/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 640 mm
1x95/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 660 mm
1x120/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 700 mm
1x150/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 720 mm
1x185/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 760 mm
1x240/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 800 mm
1x300/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 840 mm
1x400/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 900 mm
1x500/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 980 mm
1x500/50 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 980 mm
1x630/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 780 mm
1x800/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 840 mm
1x1000/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 1220 mm
1x50/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 700 mm
1x70/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 740 mm
1x95/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 760 mm
1x120/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 800 mm
1x150/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 820 mm
1x185/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 860 mm
1x240/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 900 mm
1x300/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 940 mm
1x400/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 1000 mm
1x500/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 1080 mm
1x630/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 1120 mm
1x800/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 1200 mm
1x1000/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 1340 mm

### Other Specifications

Configuration | Conductor | Insulation | Conductive Tape Below Screen | Copper Wire Screen And Tape | Non Conducting Tape Above Screen | Al Foil | Sheath | Number Of Cores And Cross Section | Minimal Storage Temperature | Colour Of Insulation | Flame Retardant | CPR Class | CE Conformity | Shape Of Conductor | Conductor Diameter | Nominal Insulation Thickness | Diameter Over Insulation | Minimum Sheath Thickness | Outer Diameter | Weight | DC Resistance At 20 °C | Capacitance | Inductance, Trefoil | Inductance In Air, Flat 1 | Inductance In Ground, Flat 1 | Conductor Shortcircuit Current | Screen Shortcircuit Current | Heating Time Constant, Trefoil | Heating Time Constant, Flat | Current Ratings In Air, Trefoil | Current Ratings In Air, Flat | Current Ratings In Ground, Trefoil | Current Ratings In Ground, Flat
--- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | ---
1x35/16 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x35/16 | -35 °C | uncoloured | no | Fca | yes | RM | 7.2 mm | 3.4 mm | 15.3 mm | 2.1 mm | 25 mm | 643 kg/km | 0.868 Ω/km | 0.22 μF/km | 0.44 | 0.61 | 0.74 | 3.3 kA | 3.2 kA | 191 | 135 | 160 | 190 | 145 | 165
1x50/16 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x50/16 | -35 °C | uncoloured | no | Fca | yes | RM | 8.3 mm | 3.4 mm | 16.4 mm | 2.1 mm | 26 mm | 712 kg/km | 0.641 Ω/km | 0.25 μF/km | 0.42 | 0.59 | 0.71 | 4.7 kA | 3.2 kA | 273 | 193 | 183 | 219 | 171 | 194
1x70/16 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x70/16 | -35 °C | uncoloured | no | Fca | yes | RM | 9.8 mm | 3.4 mm | 17.9 mm | 2.1 mm | 27 mm | 796 kg/km | 0.443 Ω/km | 0.28 μF/km | 0.4 | 0.57 | 0.68 | 6.6 kA | 3.2 kA | 348 | 247 | 228 | 273 | 208 | 236
1x95/16 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x95/16 | -35 °C | uncoloured | no | Fca | yes | RM | 11.3 mm | 3.4 mm | 19.4 mm | 2.1 mm | 29 mm | 902 kg/km | 0.32 Ω/km | 0.31 μF/km | 0.38 | 0.55 | 0.65 | 9 kA | 3.2 kA | 434 | 311 | 278 | 333 | 248 | 281
1x120/16 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x120/16 | -35 °C | uncoloured | no | Fca | yes | RM | 12.8 mm | 3.4 mm | 20.9 mm | 2.1 mm | 30 mm | 1009 kg/km | 0.253 Ω/km | 0.34 μF/km | 0.36 | 0.54 | 0.63 | 11.3 kA | 3.2 kA | 522 | 375 | 321 | 384 | 283 | 318
1x150/25 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x150/25 | -35 °C | uncoloured | no | Fca | yes | RM | 14.2 mm | 3.4 mm | 22.3 mm | 2.1 mm | 32 mm | 1193 kg/km | 0.206 Ω/km | 0.36 μF/km | 0.35 | 0.51 | 0.6 | 14.2 kA | 5 kA | 644 | 479 | 364 | 432 | 315 | 350
1x185/25 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x185/25 | -35 °C | uncoloured | no | Fca | yes | RM | 15.8 mm | 3.4 mm | 23.9 mm | 2.1 mm | 33 mm | 1341 kg/km | 0.164 Ω/km | 0.4 μF/km | 0.34 | 0.5 | 0.58 | 17.5 kA | 5 kA | 747 | 563 | 418 | 496 | 357 | 394
1x240/25 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x240/25 | -35 °C | uncoloured | no | Fca | yes | RM | 18.1 mm | 3.4 mm | 26.2 mm | 2.1 mm | 36 mm | 1546 kg/km | 0.125 Ω/km | 0.44 μF/km | 0.33 | 0.48 | 0.56 | 22.7 kA | 5 kA | 909 | 699 | 494 | 583 | 413 | 452
1x300/25 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x300/25 | -35 °C | uncoloured | no | Fca | yes | RM | 20.2 mm | 3.4 mm | 28.3 mm | 2.1 mm | 38 mm | 1797 kg/km | 0.1 Ω/km | 0.48 μF/km | 0.32 | 0.47 | 0.54 | 28.4 kA | 5 kA | 1098 | 865 | 568 | 666 | 466 | 506
1x400/35 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x400/35 | -35 °C | uncoloured | no | Fca | yes | RM | 23.3 mm | 3.4 mm | 31.4 mm | 2.1 mm | 41 mm | 2222 kg/km | 0.0778 Ω/km | 0.54 μF/km | 0.3 | 0.45 | 0.5 | 37.8 kA | 7 kA | 1474 | 1241 | 660 | 755 | 529 | 558
1x500/35 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x500/35 | -35 °C | uncoloured | no | Fca | yes | RM | 26.5 mm | 3.4 mm | 34.6 mm | 2.1 mm | 44 mm | 2599 kg/km | 0.0605 Ω/km | 0.61 μF/km | 0.29 | 0.44 | 0.48 | 47.3 kA | 7 kA | 1740 | 1525 | 767 | 868 | 602 | 627
1x630/35 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x630/35 | -35 °C | uncoloured | no | Fca | yes | RM | 29.9 mm | 3.4 mm | 38 mm | 2.1 mm | 47 mm | 3062 kg/km | 0.0469 Ω/km | 0.67 μF/km | 0.27 | 0.43 | 0.46 | 59.6 kA | 7 kA | 2131 | 1895 | 861 | 913 | 690 | 666
1x800/35 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x800/35 | -35 °C | uncoloured | no | Fca | yes | RM | 34.2 mm | 3.4 mm | 42.3 mm | 2.4 mm | 52 mm | 3686 kg/km | 0.0367 Ω/km | 0.76 μF/km | 0.26 | 0.42 | 0.45 | 75.6 kA | 7 kA | 2673 | 2461 | 976 | 1017 | 764 | 728
1x1000/35 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x1000/35 | -35 °C | uncoloured | no | Fca | yes | RM | 38.1 mm | 3.4 mm | 46.2 mm | 2.4 mm | 56 mm | 4372 kg/km | 0.0291 Ω/km | 0.84 μF/km | 0.25 | 0.4 | 0.42 | 94 kA | 7 kA | 3505 | 3157 | 1187 | 1270 | 852 | 842
1x50/16 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x50/16 | -35 °C | uncoloured | no | Fca | yes | RM | 8.3 mm | 5.5 mm | 20.6 mm | 2.1 mm | 30 mm | 876 kg/km | 0.641 Ω/km | 0.17 μF/km | 0.45 | 0.62 | 0.72 | 4.7 kA | 3.2 kA | 266 | 196 | 185 | 219 | 172 | 195
1x70/16 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x70/16 | -35 °C | uncoloured | no | Fca | yes | RM | 9.8 mm | 5.5 mm | 22.1 mm | 2.1 mm | 32 mm | 982 kg/km | 0.443 Ω/km | 0.19 μF/km | 0.42 | 0.6 | 0.69 | 6.6 kA | 3.2 kA | 339 | 251 | 231 | 273 | 210 | 237
1x95/16 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x95/16 | -35 °C | uncoloured | no | Fca | yes | RM | 11.3 mm | 5.5 mm | 23.6 mm | 2.1 mm | 33 mm | 1101 kg/km | 0.32 Ω/km | 0.21 μF/km | 0.41 | 0.58 | 0.66 | 9 kA | 3.2 kA | 426 | 318 | 280 | 332 | 251 | 282
1x120/16 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x120/16 | -35 °C | uncoloured | no | Fca | yes | RM | 12.8 mm | 5.5 mm | 25.1 mm | 2.1 mm | 35 mm | 1217 kg/km | 0.253 Ω/km | 0.23 μF/km | 0.39 | 0.56 | 0.64 | 11.3 kA | 3.2 kA | 515 | 386 | 323 | 384 | 285 | 319
1x150/25 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x150/25 | -35 °C | uncoloured | no | Fca | yes | RM | 14.2 mm | 5.5 mm | 26.5 mm | 2.1 mm | 36 mm | 1412 kg/km | 0.206 Ω/km | 0.25 μF/km | 0.38 | 0.54 | 0.61 | 14.2 kA | 5 kA | 634 | 488 | 366 | 432 | 319 | 352
1x185/25 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x185/25 | -35 °C | uncoloured | no | Fca | yes | RM | 15.8 mm | 5.5 mm | 28.1 mm | 2.1 mm | 38 mm | 1568 kg/km | 0.164 Ω/km | 0.27 μF/km | 0.36 | 0.53 | 0.59 | 17.5 kA | 5 kA | 733 | 574 | 420 | 494 | 361 | 396
1x240/25 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x240/25 | -35 °C | uncoloured | no | Fca | yes | RM | 18.1 mm | 5.5 mm | 30.4 mm | 2.1 mm | 40 mm | 1792 kg/km | 0.125 Ω/km | 0.3 μF/km | 0.35 | 0.51 | 0.57 | 22.7 kA | 5 kA | 897 | 714 | 496 | 581 | 417 | 455
1x300/25 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x300/25 | -35 °C | uncoloured | no | Fca | yes | RM | 20.2 mm | 5.5 mm | 32.5 mm | 2.1 mm | 42 mm | 2020 kg/km | 0.1 Ω/km | 0.32 μF/km | 0.34 | 0.5 | 0.55 | 28.4 kA | 5 kA | 1080 | 877 | 569 | 663 | 471 | 510
1x400/35 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x400/35 | -35 °C | uncoloured | no | Fca | yes | RM | 23.3 mm | 5.5 mm | 35.6 mm | 2.1 mm | 45 mm | 2493 kg/km | 0.078 Ω/km | 0.36 μF/km | 0.32 | 0.47 | 0.51 | 37.8 kA | 7 kA | 1474 | 1273 | 660 | 753 | 535 | 564
1x500/35 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x500/35 | -35 °C | uncoloured | no | Fca | yes | RM | 26.5 mm | 5.5 mm | 38.8 mm | 2.1 mm | 49 mm | 2903 kg/km | 0.061 Ω/km | 0.4 μF/km | 0.3 | 0.46 | 0.49 | 47.3 kA | 7 kA | 1740 | 1541 | 766 | 866 | 609 | 634
1x500/50 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x500/50 | -35 °C | uncoloured | no | Fca | yes | RM | 26.5 mm | 5.5 mm | 38.8 mm | 2.1 mm | 49 mm | 3059 kg/km | 0.061 Ω/km | 0.4 μF/km | 0.3 | 0.44 | 0.48 | 47.3 kA | 10 kA | 1840 | 1707 | 766 | 866 | 609 | 634
1x630/35 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x630/35 | -35 °C | uncoloured | no | Fca | yes | RM | 29.9 mm | 5.5 mm | 42.2 mm | 2.4 mm | 52 mm | 3383 kg/km | 0.047 Ω/km | 0.44 μF/km | 0.29 | 0.44 | 0.48 | 59.6 kA | 7 kA | 2105 | 1947 | 866 | 900 | 705 | 668
1x800/35 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x800/35 | -35 °C | uncoloured | no | Fca | yes | RM | 34.2 mm | 5.5 mm | 46.5 mm | 2.4 mm | 56 mm | 3858 kg/km | 0.037 Ω/km | 0.49 μF/km | 0.28 | 0.43 | 0.46 | 75.6 kA | 7 kA | 2631 | 2503 | 984 | 1008 | 767 | 734
1x1000/35 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x1000/35 | -35 °C | uncoloured | no | Fca | yes | RM | 38.1 mm | 5.5 mm | 50.4 mm | 2.4 mm | 61 mm | 4824 kg/km | 0.0291 Ω/km | 0.55 μF/km | 0.28 | 0.42 | 0.45 | 94 kA | 7 kA | 4323 | 3771 | 1187 | 1262 | 863 | 852
1x50/16 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x50/16 | -35 °C | uncoloured | no | Fca | yes | RM | 8.3 mm | 8 mm | 25.6 mm | 2.1 mm | 35 mm | 1100 kg/km | 0.641 Ω/km | 0.13 μF/km | 0.48 | 0.65 | 0.73 | 4.7 kA | 3.2 kA | 261 | 200 | 187 | 219 | 174 | 195
1x70/16 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x70/16 | -35 °C | uncoloured | no | Fca | yes | RM | 9.8 mm | 8 mm | 27.1 mm | 2.1 mm | 37 mm | 1213 kg/km | 0.443 Ω/km | 0.15 μF/km | 0.45 | 0.63 | 0.7 | 6.6 kA | 3.2 kA | 334 | 257 | 232 | 273 | 213 | 238
1x95/16 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x95/16 | -35 °C | uncoloured | no | Fca | yes | RM | 11.3 mm | 8 mm | 28.6 mm | 2.1 mm | 38 mm | 1339 kg/km | 0.32 Ω/km | 0.16 μF/km | 0.43 | 0.61 | 0.67 | 9 kA | 3.2 kA | 420 | 325 | 282 | 331 | 254 | 283
1x120/16 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x120/16 | -35 °C | uncoloured | no | Fca | yes | RM | 12.8 mm | 8 mm | 30.1 mm | 2.1 mm | 40 mm | 1463 kg/km | 0.253 Ω/km | 0.17 μF/km | 0.42 | 0.59 | 0.65 | 11.3 kA | 3.2 kA | 506 | 393 | 325 | 382 | 289 | 321
1x150/25 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x150/25 | -35 °C | uncoloured | no | Fca | yes | RM | 14.2 mm | 8 mm | 31.5 mm | 2.1 mm | 41 mm | 1660 kg/km | 0.206 Ω/km | 0.19 μF/km | 0.4 | 0.57 | 0.62 | 14.2 kA | 5 kA | 625 | 500 | 367 | 429 | 322 | 354
1x185/25 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x185/25 | -35 °C | uncoloured | no | Fca | yes | RM | 15.8 mm | 8 mm | 33.1 mm | 2.1 mm | 43 mm | 1837 kg/km | 0.164 Ω/km | 0.2 μF/km | 0.39 | 0.55 | 0.6 | 17.5 kA | 5 kA | 726 | 590 | 421 | 492 | 364 | 399
1x240/25 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x240/25 | -35 °C | uncoloured | no | Fca | yes | RM | 18.1 mm | 8 mm | 35.4 mm | 2.1 mm | 45 mm | 2049 kg/km | 0.125 Ω/km | 0.22 μF/km | 0.37 | 0.53 | 0.58 | 22.7 kA | 5 kA | 890 | 733 | 496 | 578 | 422 | 458
1x300/25 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x300/25 | -35 °C | uncoloured | no | Fca | yes | RM | 20.2 mm | 8 mm | 37.5 mm | 2.1 mm | 47 mm | 2336 kg/km | 0.1 Ω/km | 0.24 μF/km | 0.36 | 0.52 | 0.56 | 28.4 kA | 5 kA | 1062 | 889 | 568 | 659 | 476 | 514
1x400/35 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x400/35 | -35 °C | uncoloured | no | Fca | yes | RM | 23.3 mm | 8 mm | 40.6 mm | 2.1 mm | 50 mm | 2842 kg/km | 0.0778 Ω/km | 0.27 μF/km | 0.34 | 0.49 | 0.52 | 37.8 kA | 7 kA | 1453 | 1305 | 659 | 750 | 541 | 570
1x500/35 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x500/35 | -35 °C | uncoloured | no | Fca | yes | RM | 26.5 mm | 8 mm | 43.8 mm | 2.4 mm | 54 mm | 3269 kg/km | 0.0605 Ω/km | 0.29 μF/km | 0.32 | 0.48 | 0.5 | 47.3 kA | 7 kA | 1724 | 1575 | 764 | 861 | 616 | 642
1x630/35 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x630/35 | -35 °C | uncoloured | no | Fca | yes | RM | 29.9 mm | 8 mm | 47.2 mm | 2.4 mm | 56 mm | 3590 kg/km | 0.0469 Ω/km | 0.32 μF/km | 0.31 | 0.46 | 0.48 | 59.6 kA | 7 kA | 2105 | 2000 | 866 | 889 | 692 | 653
1x800/35 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x800/35 | -35 °C | uncoloured | no | Fca | yes | RM | 34.2 mm | 8 mm | 51.5 mm | 2.4 mm | 60 mm | 4284 kg/km | 0.0367 Ω/km | 0.36 μF/km | 0.3 | 0.45 | 0.46 | 75.6 kA | 7 kA | 2631 | 2546 | 984 | 1000 | 770 | 731
1x1000/35 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | Yes | PE | 1x1000/35 | -35 °C | uncoloured | no | Fca | yes | RM | 38.1 mm | 8 mm | 55.4 mm | 2.4 mm | 67 mm | 5327 kg/km | 0.0291 Ω/km | 0.39 μF/km | 0.3 | 0.44 | 0.45 | 94 kA | 7 kA | 3302 | 3152 | 1196 | 1256 | 878 | 863

## Related products

- ## NA2XS(F)2Y

- ## NA2XSY

- ## N2XS(F)2Y

- ## NA2XS2Y

Share Share Share Pin
Close Menu

#### KLZ Cables

Raiffeisenstraße 22
73630 Remshalden

[email protected]

../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-salient-social-js-salient-social.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-build-third-party-jquery.easing.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-build-third-party-jquery.mousewheel.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-build-priority.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-build-third-party-transit.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-build-third-party-waypoints.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-build-third-party-imagesLoaded.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-build-third-party-hoverintent.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-build-third-party-jquery.fancybox.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-build-third-party-anime.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-build-third-party-superfish.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-build-init.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-build-nectar-smooth-scroll.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-build-third-party-flickity.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-build-nectar-single-product.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-third-party-touchswipe.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-js-front-end-breeze-lazy-load.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-sourcebuster-sourcebuster.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-frontend-order-attribution.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-build-nectar-delay-javascript.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-formidable-pro-js-frm.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-dist-hooks.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xsf-1-45065-js-build-gtag-events.js