../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-vendor-DOMPurify-DOMPurify.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-assets-js-external-permalinks.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-js-front-end-breeze-prefetch-links.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-jquery-jquery.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-jquery-jquery-migrate.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-min-svgs-inline-vanilla-min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-zoom-jquery.zoom.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-photoswipe-photoswipe.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-photoswipe-photoswipe-ui-default.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-frontend-single-product.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-jquery-blockui-jquery.blockUI.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-js-cookie-js.cookie.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-frontend-woocommerce.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-dist-scripts-url-shortify.js
Skip to main content
Hit enter to search or ESC to close
Close Search

# N2XS(F)2Y

The N2XS(F)2Y cable is a longitudinally watertight medium-voltage cable with a copper conductor, XLPE insulation, and a durable PE sheath. It combines high electrical safety with a rugged outer layer, making it ideal for demanding grid operation applications.

Request Cable
Email *
Request *
If you are human, leave this field blank.
SKU: N2XS(F)2Y-medium-voltage-cables Category: Medium Voltage Cables

- Description

## Description

### Designed for high-performance network environments

The N2XS(F)2Y complies with common standards DIN VDE 0276-620, HD 620 S2 and IEC 60502, and is suitable for installation indoors, in cable ducts, outdoors, in water, underground, and on cable trays. This cable proves its strengths especially in utility grids, industrial plants, and power stations – wherever durability, watertightness, and safety are essential.

### Structure and technical characteristics

Inside is a bare, multi-stranded copper conductor (Class 2), surrounded by an extruded XLPE insulation with inner and bonded outer conductive layer. A longitudinally watertight, conductive tape, a copper wire screen with counter helix, and an additional longitudinally watertight layer ensure the design’s integrity. The black PE outer sheath (Type DMP2) provides high mechanical strength.

### Applications and benefits

The N2XS(F)2Y is suitable for underground installation, resistant to aggressive environmental conditions, and withstands temperatures up to +90 °C in continuous operation and +250 °C in short-circuit conditions. It is free from silicone and cadmium-containing substances and, thanks to its partial discharge-free design, particularly suitable for networks with the highest demands on electrical operational safety and longevity.

## Datasheet

Configuration | Rated Voltage | Test Voltage | Maximal Short Circuit Temperature | Maximal Operating Conductor Temperature | Minimal Temperature For Laying | Operating Temperature Range | Colour Of Sheath | Packaging | RoHS/REACH | Bending Radius
--- | --- | --- | --- | --- | --- | --- | --- | --- | --- | ---
1x50/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 375 mm
1x70/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 390 mm
1x95/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 420 mm
1x120/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 450 mm
1x150/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 465 mm
1x185/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 480 mm
1x240/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 525 mm
1x300/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 555 mm
1x400/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 600 mm
1x500/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 645 mm
1x35/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 420 mm
1x50/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 435 mm
1x70/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 465 mm
1x95/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 480 mm
1x120/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 510 mm
1x150/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 525 mm
1x185/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 555 mm
1x240/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 585 mm
1x300/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 630 mm
1x400/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 660 mm
1x500/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 705 mm
1x50/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 510 mm
1x70/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 540 mm
1x95/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 555 mm
1x120/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 585 mm
1x150/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 600 mm
1x185/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 630 mm
1x240/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 660 mm
1x300/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 705 mm
1x400/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 735 mm
1x500/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 795 mm

### Other Specifications

Configuration | Conductor | Insulation | Conductive Tape Below Screen | Copper Wire Screen And Tape | Non Conducting Tape Above Screen | Al Foil | Sheath | Number Of Cores And Cross Section | Minimal Storage Temperature | Colour Of Insulation | Flame Retardant | CPR Class | CE Conformity | Shape Of Conductor | Conductor Diameter | Nominal Insulation Thickness | Diameter Over Insulation | Minimum Sheath Thickness | Outer Diameter | Weight | DC Resistance At 20 °C | Capacitance | Inductance, Trefoil | Inductance In Ground, Flat 1 | Conductor Shortcircuit Current | Screen Shortcircuit Current | Heating Time Constant, Trefoil | Heating Time Constant, Flat | Current Ratings In Air, Trefoil | Current Ratings In Air, Flat | Current Ratings In Ground, Trefoil | Current Ratings In Ground, Flat | Inductance In Air, Flat 1
--- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | ---
1x50/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x50/16 | –35 °C | uncoloured | no | Fca | yes | RM | 8.2 mm | 3.4 mm | 16.3 mm | 2.1 mm | 26 mm | 928 kg/km | 0.387 Ω/km | 0.24 μF/km | 0.41 | 0.71 | 7.1 kA | 3.2 kA | 385 | 275 | 238 | 282 | 220 | 249 | N/A
1x70/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x70/16 | –35 °C | uncoloured | no | Fca | yes | RM | 9.8 mm | 3.4 mm | 17.9 mm | 2.1 mm | 26 mm | 1155 kg/km | 0.268 Ω/km | 0.28 μF/km | 0.39 | 0.67 | 10 kA | 3.2 kA | 491 | 353 | 294 | 350 | 268 | 302 | N/A
1x95/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x95/16 | –35 °C | uncoloured | no | Fca | yes | RM | 11.3 mm | 3.4 mm | 19.4 mm | 2.1 mm | 28 mm | 1410 kg/km | 0.193 Ω/km | 0.3 μF/km | 0.37 | 0.65 | 13.6 kA | 3.2 kA | 618 | 450 | 358 | 426 | 320 | 359 | N/A
1x120/16 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x120/16 | –35 °C | uncoloured | no | Fca | yes | RM | 12.8 mm | 3.4 mm | 20.9 mm | 2.1 mm | 30 mm | 1683 kg/km | 0.153 Ω/km | 0.34 μF/km | 0.36 | 0.62 | 17.1 kA | 3.2 kA | 744 | 550 | 413 | 491 | 363 | 405 | N/A
1x150/25 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x150/25 | –35 °C | uncoloured | no | Fca | yes | RM | 14.2 mm | 3.4 mm | 22.3 mm | 2.1 mm | 31 mm | 2052 kg/km | 0.124 Ω/km | 0.36 μF/km | 0.34 | 0.59 | 21.4 kA | 5 kA | 927 | 719 | 468 | 549 | 405 | 442 | N/A
1x185/25 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x185/25 | –35 °C | uncoloured | no | Fca | yes | RM | 15.8 mm | 3.4 mm | 23.9 mm | 2.1 mm | 32 mm | 2384 kg/km | 0.099 Ω/km | 0.4 μF/km | 0.33 | 0.58 | 26.4 kA | 5 kA | 1094 | 866 | 535 | 625 | 456 | 493 | N/A
1x240/25 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x240/25 | –35 °C | uncoloured | no | Fca | yes | RM | 18.3 mm | 3.4 mm | 26.4 mm | 2.1 mm | 35 mm | 2964 kg/km | 0.075 Ω/km | 0.44 μF/km | 0.32 | 0.55 | 34.3 kA | 5 kA | 1327 | 1082 | 631 | 731 | 526 | 563 | N/A
1x300/25 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x300/25 | –35 °C | uncoloured | no | Fca | yes | RM | 20.7 mm | 3.4 mm | 28.8 mm | 2.1 mm | 37 mm | 3624 kg/km | 0.06 Ω/km | 0.49 μF/km | 0.31 | 0.53 | 42.9 kA | 5 kA | 1582 | 1309 | 722 | 831 | 591 | 626 | N/A
1x400/35 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x400/35 | –35 °C | uncoloured | no | Fca | yes | RM | 23.3 mm | 3.4 mm | 31.4 mm | 2.1 mm | 40 mm | 4575 kg/km | 0.047 Ω/km | 0.54 μF/km | 0.29 | 0.5 | 57.2 kA | 7 kA | 2279 | 2061 | 827 | 920 | 662 | 675 | N/A
1x500/35 - 6/10 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x500/35 | –35 °C | uncoloured | no | Fca | yes | RM | 26.5 mm | 3.4 mm | 34.6 mm | 2.1 mm | 43 mm | 5598 kg/km | 0.037 Ω/km | 0.61 μF/km | 0.28 | 0.48 | 71.4 kA | 7 kA | 2803 | 2614 | 949 | 1043 | 744 | 748 | N/A
1x35/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x35/16 | -35 °C | uncoloured | no | Fca | yes | RM | 7.2 mm | 5.5 mm | 19.5 mm | 2.1 mm | 28 mm | 949 kg/km | 0.524 Ω/km | 0.16 μF/km | 0.46 | 0.74 | 5 kA | 3.2 kA | 259 | 192 | 200 | 235 | 189 | 213 | 0.64
1x50/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x50/16 | -35 °C | uncoloured | no | Fca | yes | RM | 8.2 mm | 5.5 mm | 20.5 mm | 2.1 mm | 29 mm | 1079 kg/km | 0.387 Ω/km | 0.17 μF/km | 0.44 | 0.72 | 7.1 kA | 3.2 kA | 374 | 278 | 239 | 282 | 222 | 250 | 0.62
1x70/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x70/16 | -35 °C | uncoloured | no | Fca | yes | RM | 9.8 mm | 5.5 mm | 22.1 mm | 2.1 mm | 31 mm | 1315 kg/km | 0.268 Ω/km | 0.19 μF/km | 0.42 | 0.68 | 10 kA | 3.2 kA | 477 | 358 | 297 | 351 | 271 | 303 | 0.59
1x95/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x95/16 | -35 °C | uncoloured | no | Fca | yes | RM | 11.3 mm | 5.5 mm | 23.6 mm | 2.1 mm | 32 mm | 1580 kg/km | 0.193 Ω/km | 0.21 μF/km | 0.4 | 0.66 | 13.6 kA | 3.2 kA | 600 | 458 | 361 | 426 | 323 | 360 | 0.57
1x120/16 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x120/16 | -35 °C | uncoloured | no | Fca | yes | RM | 12.8 mm | 5.5 mm | 25.1 mm | 2.1 mm | 34 mm | 1862 kg/km | 0.153 Ω/km | 0.23 μF/km | 0.38 | 0.63 | 17.1 kA | 3.2 kA | 724 | 556 | 416 | 491 | 367 | 407 | 0.55
1x150/25 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x150/25 | -35 °C | uncoloured | no | Fca | yes | RM | 14.2 mm | 5.5 mm | 26.5 mm | 2.1 mm | 35 mm | 2212 kg/km | 0.124 Ω/km | 0.25 μF/km | 0.37 | 0.6 | 21.4 kA | 5 kA | 903 | 730 | 470 | 549 | 409 | 445 | 0.53
1x185/25 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x185/25 | -35 °C | uncoloured | no | Fca | yes | RM | 15.8 mm | 5.5 mm | 28.1 mm | 2.1 mm | 37 mm | 2585 kg/km | 0.099 Ω/km | 0.27 μF/km | 0.36 | 0.59 | 26.4 kA | 5 kA | 1068 | 871 | 538 | 625 | 461 | 498 | 0.52
1x240/25 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x240/25 | -35 °C | uncoloured | no | Fca | yes | RM | 18.3 mm | 5.5 mm | 30.6 mm | 2.1 mm | 39 mm | 3181 kg/km | 0.075 Ω/km | 0.3 μF/km | 0.34 | 0.56 | 34.3 kA | 5 kA | 1309 | 1091 | 634 | 731 | 532 | 568 | 0.5
1x300/25 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x300/25 | -35 °C | uncoloured | no | Fca | yes | RM | 20.7 mm | 5.5 mm | 33 mm | 2.1 mm | 42 mm | 3851 kg/km | 0.06 Ω/km | 0.33 μF/km | 0.33 | 0.54 | 42.9 kA | 5 kA | 1582 | 1350 | 724 | 830 | 599 | 633 | 0.48
1x400/35 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x400/35 | -35 °C | uncoloured | no | Fca | yes | RM | 23.3 mm | 5.5 mm | 35.6 mm | 2.1 mm | 44 mm | 4795 kg/km | 0.047 Ω/km | 0.36 μF/km | 0.31 | 0.51 | 57.2 kA | 7 kA | 2255 | 2109 | 829 | 923 | 671 | 685 | 0.46
1x500/35 - 12/20 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x500/35 | -35 °C | uncoloured | no | Fca | yes | RM | 26.5 mm | 5.5 mm | 38.8 mm | 2.1 mm | 47 mm | 5873 kg/km | 0.037 Ω/km | 0.4 μF/km | 0.3 | 0.49 | 71.4 kA | 7 kA | 2727 | 2614 | 953 | 1045 | 754 | 760 | 0.45
1x50/16 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x50/16 | -35 °C | uncoloured | no | Fca | yes | RM | 8.2 mm | 8 mm | 25.5 mm | 2.1 mm | 34 mm | 1292 kg/km | 0.387 Ω/km | 0.13 μF/km | 0.48 | 0.73 | 7.1 kA | 3.2 kA | 365 | 283 | 241 | 282 | 225 | 251 | N/A
1x70/16 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x70/16 | -35 °C | uncoloured | no | Fca | yes | RM | 9.8 mm | 8 mm | 27.1 mm | 2.1 mm | 36 mm | 1542 kg/km | 0.268 Ω/km | 0.15 μF/km | 0.45 | 0.7 | 10 kA | 3.2 kA | 466 | 364 | 299 | 350 | 274 | 304 | N/A
1x95/16 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x95/16 | -35 °C | uncoloured | no | Fca | yes | RM | 11.3 mm | 8 mm | 28.6 mm | 2.1 mm | 37 mm | 1818 kg/km | 0.193 Ω/km | 0.16 μF/km | 0.43 | 0.67 | 13.6 kA | 3.2 kA | 589 | 464 | 363 | 425 | 327 | 362 | N/A
1x120/16 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x120/16 | -35 °C | uncoloured | no | Fca | yes | RM | 12.8 mm | 8 mm | 30.1 mm | 2.1 mm | 39 mm | 2110 kg/km | 0.153 Ω/km | 0.17 μF/km | 0.41 | 0.64 | 17.1 kA | 3.2 kA | 713 | 567 | 418 | 468 | 371 | 409 | N/A
1x150/25 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x150/25 | -35 °C | uncoloured | no | Fca | yes | RM | 14.2 mm | 8 mm | 31.5 mm | 2.1 mm | 40 mm | 2473 kg/km | 0.124 Ω/km | 0.19 μF/km | 0.4 | 0.62 | 21.4 kA | 5 kA | 893 | 740 | 472 | 548 | 414 | 449 | N/A
1x185/25 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x185/25 | -35 °C | uncoloured | no | Fca | yes | RM | 15.8 mm | 8 mm | 33.1 mm | 2.1 mm | 42 mm | 2854 kg/km | 0.099 Ω/km | 0.2 μF/km | 0.38 | 0.6 | 26.4 kA | 5 kA | 1048 | 887 | 539 | 624 | 466 | 502 | N/A
1x240/25 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x240/25 | -35 °C | uncoloured | no | Fca | yes | RM | 18.3 mm | 8 mm | 35.6 mm | 2.1 mm | 44 mm | 3468 kg/km | 0.075 Ω/km | 0.22 μF/km | 0.36 | 0.57 | 34.3 kA | 5 kA | 1283 | 1117 | 635 | 728 | 539 | 574 | N/A
1x300/25 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x300/25 | -35 °C | uncoloured | no | Fca | yes | RM | 20.7 mm | 8 mm | 38 mm | 2.1 mm | 47 mm | 4164 kg/km | 0.06 Ω/km | 0.24 μF/km | 0.35 | 0.55 | 42.9 kA | 5 kA | 1555 | 1364 | 725 | 828 | 606 | 640 | N/A
1x400/35 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x400/35 | -35 °C | uncoloured | no | Fca | yes | RM | 23.3 mm | 8 mm | 40.6 mm | 2.1 mm | 49 mm | 5131 kg/km | 0.047 Ω/km | 0.26 μF/km | 0.33 | 0.52 | 57.2 kA | 7 kA | 2206 | 2109 | 831 | 922 | 680 | 695 | N/A
1x500/35 - 18/30 kV | Copper | XLPE | Yes | Yes | Yes | No | PE | 1x500/35 | -35 °C | uncoloured | no | Fca | yes | RM | 26.5 mm | 8 mm | 43.8 mm | 2.4 mm | 53 mm | 6235 kg/km | 0.037 Ω/km | 0.29 μF/km | 0.32 | 0.5 | 71.4 kA | 7 kA | 2689 | 2652 | 953 | 1045 | 765 | 773 | N/A

## Related products

- ## N2XSY

- ## NA2XS(F)2Y

- ## N2XS(FL)2Y

- ## NA2XS(FL)2Y

Share Share Share Pin
Close Menu

#### KLZ Cables

Raiffeisenstraße 22
73630 Remshalden

[email protected]

../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-salient-social-js-salient-social.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-build-third-party-jquery.easing.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-build-third-party-jquery.mousewheel.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-build-priority.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-build-third-party-transit.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-build-third-party-waypoints.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-build-third-party-imagesLoaded.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-build-third-party-hoverintent.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-build-third-party-jquery.fancybox.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-build-third-party-anime.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-build-third-party-superfish.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-build-init.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-build-nectar-smooth-scroll.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-build-third-party-flickity.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-build-nectar-single-product.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-third-party-touchswipe.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-js-front-end-breeze-lazy-load.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-sourcebuster-sourcebuster.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-frontend-order-attribution.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-build-nectar-delay-javascript.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-formidable-pro-js-frm.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-dist-hooks.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-n2xsf2-1-44324-js-build-gtag-events.js