../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-vendor-DOMPurify-DOMPurify.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-assets-js-external-permalinks.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-js-front-end-breeze-prefetch-links.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-jquery-jquery.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-jquery-jquery-migrate.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-min-svgs-inline-vanilla-min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-zoom-jquery.zoom.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-photoswipe-photoswipe.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-photoswipe-photoswipe-ui-default.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-frontend-single-product.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-jquery-blockui-jquery.blockUI.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-js-cookie-js.cookie.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-frontend-woocommerce.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-dist-scripts-url-shortify.js
Skip to main content
Hit enter to search or ESC to close
Close Search

# NA2XS2Y

The NA2XS2Y cable is a high-performance medium-voltage cable with an aluminium conductor, XLPE insulation, and a robust PE sheath. It is perfectly suited for underground applications and impresses with its thermal load capacity, mechanical durability, and partial discharge-free design.

Request Cable
Email *
Request *
If you are human, leave this field blank.
SKU: NA2XS2Y-medium-voltage-cables Category: Medium Voltage Cables

- Description

## Description

### For harsh environments and heavy loads

The NA2XS2Y complies with DIN VDE 0276-620, HD 620 S2 and IEC 60502 standards, and is specifically designed for fixed installation indoors, in cable ducts, outdoors, in soil and water. It is commonly used in industrial facilities, switching stations, and power plants, especially where the cable is exposed to high mechanical stress during installation or operation.

### Construction and technical features

The cable features a multi-stranded aluminium conductor (Class 2 according to DIN VDE 0295 / IEC 60228). The XLPE insulation (Type DIX8) is inseparably bonded to the outer conductive layer and, together with the inner conductive layer, ensures partial discharge-free operation. The shielding consists of a copper wire braid with counter helix. The black PE sheath (Type DMP2) protects against moisture, mechanical pressure, and chemical exposure – but is not flame-retardant.

### Special features and application benefits

NA2XS2Y is suitable for underground installation and for use at temperatures as low as -20 °C. It is free from silicone and cadmium, contains no paint-wetting impairment substances, and handles a continuous operating temperature of up to +90 °C, and up to +250 °C in short-circuit conditions. The black PE sheath makes this cable the ideal high-resilience solution for permanent underground medium-voltage installations.

## Datasheet

Configuration | Rated Voltage | Test Voltage | Maximal Short Circuit Temperature | Maximal Operating Conductor Temperature | Minimal Temperature For Laying | Operating Temperature Range | Colour Of Sheath | Packaging | RoHS/REACH | Bending Radius
--- | --- | --- | --- | --- | --- | --- | --- | --- | --- | ---
1x35/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 345 mm
1x50/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 375 mm
1x70/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 390 mm
1x95/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 420 mm
1x120/16 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 435 mm
1x150/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 450 mm
1x185/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 480 mm
1x240/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 510 mm
1x300/25 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 555 mm
1x400/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 600 mm
1x500/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 645 mm
1x630/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 690 mm
1x800/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 765 mm
1x1000/35 - 6/10 kV | 6/10 kV | 21 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 855 mm
1x50/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 435 mm
1x70/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 465 mm
1x95/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 480 mm
1x120/16 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 510 mm
1x150/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 525 mm
1x185/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 555 mm
1x240/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 585 mm
1x300/25 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 615 mm
1x400/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 660 mm
1x500/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 705 mm
1x630/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 765 mm
1x800/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 840 mm
1x1000/35 - 12/20 kV | 12/20 kV | 42 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 915 mm
1x50/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 510 mm
1x70/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 540 mm
1x95/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 555 mm
1x120/16 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 585 mm
1x150/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 600 mm
1x185/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 630 mm
1x240/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 660 mm
1x300/25 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 690 mm
1x400/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 735 mm
1x500/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 795 mm
1x630/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 840 mm
1x800/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 915 mm
1x1000/35 - 18/30 kV | 18/30 kV | 63 kV | +250 °C | +90 °C | -20 °C | -35 - +90 °C | black | wooden or metal drums | N/A | 1005 mm

### Other Specifications

Configuration | Conductor | Insulation | Conductive Tape Below Screen | Copper Wire Screen And Tape | Non Conducting Tape Above Screen | Al Foil | Sheath | Number Of Cores And Cross Section | Minimal Storage Temperature | Colour Of Insulation | Flame Retardant | CPR Class | CE Conformity | Shape Of Conductor | Conductor Diameter | Nominal Insulation Thickness | Diameter Over Insulation | Minimum Sheath Thickness | Outer Diameter | Weight | DC Resistance At 20 °C | Capacitance | Inductance, Trefoil | Inductance In Air, Flat 1 | Inductance In Ground, Flat 1 | Conductor Shortcircuit Current | Screen Shortcircuit Current | Heating Time Constant, Trefoil | Heating Time Constant, Flat | Current Ratings In Air, Trefoil | Current Ratings In Air, Flat | Current Ratings In Ground, Trefoil | Current Ratings In Ground, Flat
--- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | --- | ---
1x35/16 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x35/16 | -35 °C | uncoloured | no | Fca | yes | RM | 7.2 mm | 3.4 mm | 15.3 mm | 2.1 mm | 23 mm | 563 kg/km | 0.868 Ω/km | 0.22 μF/km | 0.43 | 0.61 | 0.73 | 3.3 kA | 3.2 kA | 194 | 136 | 153 | 182 | 145 | 165
1x50/16 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x50/16 | -35 °C | uncoloured | no | Fca | yes | RM | 8.3 mm | 3.4 mm | 16.4 mm | 2.1 mm | 25 mm | 624 kg/km | 0.641 Ω/km | 0.25 μF/km | 0.42 | 0.6 | 0.71 | 4.7 kA | 3.2 kA | 270 | 191 | 183 | 219 | 171 | 194
1x70/16 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x70/16 | -35 °C | uncoloured | no | Fca | yes | RM | 9.8 mm | 3.4 mm | 17.9 mm | 2.1 mm | 26 mm | 707 kg/km | 0.443 Ω/km | 0.28 μF/km | 0.39 | 0.56 | 0.68 | 6.6 kA | 3.2 kA | 353 | 249 | 228 | 273 | 208 | 236
1x95/16 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x95/16 | -35 °C | uncoloured | no | Fca | yes | RM | 11.3 mm | 3.4 mm | 19.4 mm | 2.1 mm | 28 mm | 808 kg/km | 0.32 Ω/km | 0.31 μF/km | 0.38 | 0.55 | 0.65 | 9 kA | 3.2 kA | 440 | 314 | 278 | 333 | 248 | 281
1x120/16 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x120/16 | -35 °C | uncoloured | no | Fca | yes | RM | 12.8 mm | 3.4 mm | 20.9 mm | 2.1 mm | 29 mm | 905 kg/km | 0.253 Ω/km | 0.34 μF/km | 0.36 | 0.53 | 0.63 | 11.3 kA | 3.2 kA | 528 | 379 | 321 | 384 | 283 | 318
1x150/25 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x150/25 | -35 °C | uncoloured | no | Fca | yes | RM | 14.2 mm | 3.4 mm | 22.3 mm | 2.1 mm | 30 mm | 1085 kg/km | 0.206 Ω/km | 0.36 μF/km | 0.35 | 0.51 | 0.6 | 14.2 kA | 5 kA | 655 | 486 | 364 | 432 | 315 | 350
1x185/25 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x185/25 | -35 °C | uncoloured | no | Fca | yes | RM | 15.8 mm | 3.4 mm | 23.9 mm | 2.1 mm | 32 mm | 1226 kg/km | 0.164 Ω/km | 0.4 μF/km | 0.33 | 0.5 | 0.58 | 17.5 kA | 5 kA | 760 | 574 | 418 | 496 | 357 | 394
1x240/25 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x240/25 | -35 °C | uncoloured | no | Fca | yes | RM | 18.1 mm | 3.4 mm | 26.2 mm | 2.1 mm | 34 mm | 1423 kg/km | 0.125 Ω/km | 0.44 μF/km | 0.32 | 0.48 | 0.55 | 22.7 kA | 5 kA | 928 | 710 | 494 | 583 | 413 | 452
1x300/25 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x300/25 | -35 °C | uncoloured | no | Fca | yes | RM | 20.2 mm | 3.4 mm | 28.3 mm | 2.1 mm | 37 mm | 1666 kg/km | 0.1 Ω/km | 0.48 μF/km | 0.31 | 0.47 | 0.54 | 28.4 kA | 5 kA | 1098 | 859 | 568 | 666 | 466 | 506
1x400/35 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x400/35 | -35 °C | uncoloured | no | Fca | yes | RM | 23.3 mm | 3.4 mm | 31.4 mm | 2.1 mm | 40 mm | 2082 kg/km | 0.0778 Ω/km | 0.54 μF/km | 0.3 | 0.45 | 0.5 | 37.8 kA | 7 kA | 1496 | 1262 | 660 | 755 | 529 | 558
1x500/35 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x500/35 | -35 °C | uncoloured | no | Fca | yes | RM | 26.5 mm | 3.4 mm | 34.6 mm | 2.1 mm | 43 mm | 2447 kg/km | 0.0605 Ω/km | 0.61 μF/km | 0.28 | 0.43 | 0.48 | 47.3 kA | 7 kA | 1773 | 1508 | 767 | 868 | 602 | 627
1x630/35 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x630/35 | -35 °C | uncoloured | no | Fca | yes | RM | 29.9 mm | 3.4 mm | 38 mm | 2.1 mm | 46 mm | 2909 kg/km | 0.0469 Ω/km | 0.66 μF/km | 0.27 | 0.42 | 0.46 | 59.6 kA | 7 kA | 2158 | 1895 | 855 | 913 | 685 | 668
1x800/35 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x800/35 | -35 °C | uncoloured | no | Fca | yes | RM | 34.2 mm | 3.4 mm | 42.3 mm | 2.4 mm | 51 mm | 3520 kg/km | 0.0367 Ω/km | 0.76 μF/km | 0.26 | 0.41 | 0.44 | 75.6 kA | 7 kA | 2716 | 2461 | 968 | 1017 | 764 | 731
1x1000/35 - 6/10 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x1000/35 | -35 °C | uncoloured | no | Fca | yes | RM | 38.1 mm | 3.4 mm | 46.2 mm | 2.4 mm | 57 mm | 4422 kg/km | 0.0291 Ω/km | 0.84 μF/km | 0.25 | 0.4 | 0.42 | 94 kA | 7 kA | 3505 | 3157 | 1187 | 1270 | 852 | 842
1x50/16 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x50/16 | -35 °C | uncoloured | no | Fca | yes | RM | 8.3 mm | 5.5 mm | 20.6 mm | 2.1 mm | 29 mm | 795 kg/km | 0.641 Ω/km | 0.17 μF/km | 0.44 | 0.62 | 0.72 | 4.7 kA | 3.2 kA | 269 | 198 | 185 | 219 | 172 | 195
1x70/16 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x70/16 | -35 °C | uncoloured | no | Fca | yes | RM | 9.8 mm | 5.5 mm | 22.1 mm | 2.1 mm | 31 mm | 888 kg/km | 0.443 Ω/km | 0.19 μF/km | 0.42 | 0.59 | 0.69 | 6.6 kA | 3.2 kA | 344 | 254 | 231 | 273 | 210 | 237
1x95/16 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x95/16 | -35 °C | uncoloured | no | Fca | yes | RM | 11.3 mm | 5.5 mm | 23.6 mm | 2.1 mm | 32 mm | 999 kg/km | 0.32 Ω/km | 0.21 μF/km | 0.4 | 0.57 | 0.66 | 9 kA | 3.2 kA | 433 | 321 | 280 | 332 | 251 | 282
1x120/16 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x120/16 | -35 °C | uncoloured | no | Fca | yes | RM | 12.8 mm | 5.5 mm | 25.1 mm | 2.1 mm | 34 mm | 1108 kg/km | 0.253 Ω/km | 0.23 μF/km | 0.38 | 0.56 | 0.64 | 11.3 kA | 3.2 kA | 520 | 388 | 323 | 384 | 285 | 319
1x150/25 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x150/25 | -35 °C | uncoloured | no | Fca | yes | RM | 14.2 mm | 5.5 mm | 26.5 mm | 2.1 mm | 35 mm | 1301 kg/km | 0.206 Ω/km | 0.25 μF/km | 0.37 | 0.54 | 0.61 | 14.2 kA | 5 kA | 643 | 495 | 366 | 432 | 319 | 352
1x185/25 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x185/25 | -35 °C | uncoloured | no | Fca | yes | RM | 15.8 mm | 5.5 mm | 28.1 mm | 2.1 mm | 37 mm | 1452 kg/km | 0.164 Ω/km | 0.27 μF/km | 0.36 | 0.52 | 0.59 | 17.5 kA | 5 kA | 749 | 583 | 420 | 494 | 361 | 396
1x240/25 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x240/25 | -35 °C | uncoloured | no | Fca | yes | RM | 18.1 mm | 5.5 mm | 30.4 mm | 2.1 mm | 39 mm | 1671 kg/km | 0.125 Ω/km | 0.3 μF/km | 0.34 | 0.5 | 0.56 | 22.7 kA | 5 kA | 913 | 726 | 496 | 581 | 417 | 455
1x300/25 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x300/25 | -35 °C | uncoloured | no | Fca | yes | RM | 20.2 mm | 5.5 mm | 32.5 mm | 2.1 mm | 41 mm | 1893 kg/km | 0.1 Ω/km | 0.32 μF/km | 0.33 | 0.49 | 0.55 | 28.4 kA | 5 kA | 1098 | 883 | 569 | 663 | 471 | 510
1x400/35 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x400/35 | -35 °C | uncoloured | no | Fca | yes | RM | 23.3 mm | 5.5 mm | 35.6 mm | 2.1 mm | 44 mm | 2357 kg/km | 0.078 Ω/km | 0.36 μF/km | 0.31 | 0.47 | 0.51 | 37.8 kA | 7 kA | 1485 | 1273 | 660 | 753 | 535 | 564
1x500/35 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x500/35 | -35 °C | uncoloured | no | Fca | yes | RM | 26.5 mm | 5.5 mm | 38.8 mm | 2.1 mm | 47 mm | 2757 kg/km | 0.061 Ω/km | 0.4 μF/km | 0.3 | 0.45 | 0.49 | 47.3 kA | 7 kA | 1757 | 1541 | 766 | 866 | 609 | 634
1x630/35 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x630/35 | -35 °C | uncoloured | no | Fca | yes | RM | 29.9 mm | 5.5 mm | 42.2 mm | 2.4 mm | 51 mm | 3227 kg/km | 0.047 Ω/km | 0.44 μF/km | 0.29 | 0.44 | 0.47 | 59.6 kA | 7 kA | 2131 | 1947 | 861 | 900 | 690 | 668
1x800/35 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x800/35 | -35 °C | uncoloured | no | Fca | yes | RM | 34.2 mm | 5.5 mm | 46.5 mm | 2.4 mm | 56 mm | 3856 kg/km | 0.037 Ω/km | 0.49 μF/km | 0.28 | 0.43 | 0.45 | 75.6 kA | 7 kA | 2673 | 2503 | 976 | 1008 | 764 | 731
1x1000/35 - 12/20 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x1000/35 | -35 °C | uncoloured | no | Fca | yes | RM | 38.1 mm | 5.5 mm | 50.4 mm | 2.4 mm | 61 mm | 4824 kg/km | 0.0291 Ω/km | 0.55 μF/km | 0.28 | 0.42 | 0.45 | 94 kA | 7 kA | 4323 | 3771 | 1187 | 1262 | 863 | 852
1x50/16 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x50/16 | -35 °C | uncoloured | no | Fca | yes | RM | 8.3 mm | 8 mm | 25.6 mm | 2.1 mm | 34 mm | 1009 kg/km | 0.641 Ω/km | 0.13 μF/km | 0.48 | 0.65 | 0.73 | 4.7 kA | 3.2 kA | 263 | 202 | 187 | 219 | 174 | 195
1x70/16 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x70/16 | -35 °C | uncoloured | no | Fca | yes | RM | 9.8 mm | 8 mm | 27.1 mm | 2.1 mm | 36 mm | 1115 kg/km | 0.443 Ω/km | 0.15 μF/km | 0.45 | 0.62 | 0.7 | 6.6 kA | 3.2 kA | 337 | 258 | 232 | 273 | 213 | 238
1x95/16 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x95/16 | -35 °C | uncoloured | no | Fca | yes | RM | 11.3 mm | 8 mm | 28.6 mm | 2.1 mm | 37 mm | 1237 kg/km | 0.32 Ω/km | 0.16 μF/km | 0.43 | 0.6 | 0.67 | 9 kA | 3.2 kA | 424 | 327 | 282 | 331 | 254 | 283
1x120/16 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x120/16 | -35 °C | uncoloured | no | Fca | yes | RM | 12.8 mm | 8 mm | 30.1 mm | 2.1 mm | 39 mm | 1357 kg/km | 0.253 Ω/km | 0.17 μF/km | 0.41 | 0.58 | 0.64 | 11.3 kA | 3.2 kA | 520 | 400 | 325 | 382 | 289 | 321
1x150/25 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x150/25 | -35 °C | uncoloured | no | Fca | yes | RM | 14.2 mm | 8 mm | 31.5 mm | 2.1 mm | 40 mm | 1561 kg/km | 0.206 Ω/km | 0.19 μF/km | 0.4 | 0.56 | 0.62 | 14.2 kA | 5 kA | 631 | 501 | 367 | 429 | 322 | 354
1x185/25 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x185/25 | -35 °C | uncoloured | no | Fca | yes | RM | 15.8 mm | 8 mm | 33.1 mm | 2.1 mm | 42 mm | 1721 kg/km | 0.164 Ω/km | 0.2 μF/km | 0.39 | 0.55 | 0.6 | 17.5 kA | 5 kA | 733 | 592 | 421 | 492 | 364 | 399
1x240/25 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x240/25 | -35 °C | uncoloured | no | Fca | yes | RM | 18.1 mm | 8 mm | 35.4 mm | 2.1 mm | 44 mm | 1956 kg/km | 0.125 Ω/km | 0.22 μF/km | 0.37 | 0.53 | 0.58 | 22.7 kA | 5 kA | 897 | 733 | 496 | 578 | 422 | 458
1x300/25 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x300/25 | -35 °C | uncoloured | no | Fca | yes | RM | 20.2 mm | 8 mm | 37.5 mm | 2.1 mm | 46 mm | 2203 kg/km | 0.1 Ω/km | 0.24 μF/km | 0.36 | 0.52 | 0.56 | 28.4 kA | 5 kA | 1068 | 895 | 568 | 659 | 476 | 514
1x400/35 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x400/35 | -35 °C | uncoloured | no | Fca | yes | RM | 23.3 mm | 8 mm | 40.6 mm | 2.1 mm | 49 mm | 2693 kg/km | 0.078 Ω/km | 0.26 μF/km | 0.34 | 0.49 | 0.52 | 37.8 kA | 7 kA | 1453 | 1294 | 659 | 750 | 541 | 570
1x500/35 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x500/35 | -35 °C | uncoloured | no | Fca | yes | RM | 26.5 mm | 8 mm | 43.8 mm | 2.4 mm | 53 mm | 3119 kg/km | 0.061 Ω/km | 0.29 μF/km | 0.32 | 0.48 | 0.5 | 47.3 kA | 7 kA | 1740 | 1575 | 764 | 861 | 616 | 642
1x630/35 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x630/35 | -35 °C | uncoloured | no | Fca | yes | RM | 29.9 mm | 8 mm | 47.2 mm | 2.4 mm | 56 mm | 3617 kg/km | 0.047 Ω/km | 0.32 μF/km | 0.31 | 0.46 | 0.48 | 59.6 kA | 7 kA | 2131 | 2000 | 861 | 889 | 690 | 668
1x800/35 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x800/35 | -35 °C | uncoloured | no | Fca | yes | RM | 34.2 mm | 8 mm | 51.5 mm | 2.4 mm | 61 mm | 4300 kg/km | 0.037 Ω/km | 0.36 μF/km | 0.3 | 0.45 | 0.46 | 75.6 kA | 7 kA | 2631 | 2546 | 984 | 1000 | 770 | 734
1x1000/35 - 18/30 kV | Aluminum | XLPE | Yes | Yes | Yes | No | PE | 1x1000/35 | -35 °C | uncoloured | no | Fca | yes | RM | 38.1 mm | 8 mm | 55.4 mm | 2.4 mm | 67 mm | 5326 kg/km | 0.0291 Ω/km | 0.39 μF/km | 0.3 | 0.44 | 0.45 | 94 kA | 7 kA | 3302 | 3152 | 1196 | 1256 | 878 | 863

## Related products

- ## NA2XS(F)2Y

- ## N2XSY

- ## NA2XSY

- ## NA2XS(FL)2Y

Share Share Share Pin
Close Menu

#### KLZ Cables

Raiffeisenstraße 22
73630 Remshalden

[email protected]

../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-salient-social-js-salient-social.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-build-third-party-jquery.easing.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-build-third-party-jquery.mousewheel.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-build-priority.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-build-third-party-transit.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-build-third-party-waypoints.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-build-third-party-imagesLoaded.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-build-third-party-hoverintent.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-build-third-party-jquery.fancybox.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-build-third-party-anime.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-build-third-party-superfish.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-build-init.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-build-nectar-smooth-scroll.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-build-third-party-flickity.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-build-nectar-single-product.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-third-party-touchswipe.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-js-front-end-breeze-lazy-load.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-sourcebuster-sourcebuster.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-frontend-order-attribution.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-build-nectar-delay-javascript.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-formidable-pro-js-frm.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-dist-hooks.min.js
../../../../wp-content/cache/breeze-minification/js/breeze_products-power-cables-medium-voltage-cables-na2xs2-1-44743-js-build-gtag-events.js